We were more than pleased with the service we received from Dave Taylor and Bay Area. The repair was made quickly and at a reasonable price. We would definitely recommend Bay Area to others.
Technician was very professional and fixed the issue quickly.
bay area is the best! All your techs are top notch.
Woke up to cold house on Sunday morning. Called bay area A/C Robert arrived within 2 hours. Had heat within 15 min. Heat very important to senior's. Thanks Robert.
The technician arrived as promised, explained what he needed to do, and did it.
service person was super
This is An Estimate to Install A New Carrier 14.5 seer Package Unit Heat Pump.
Service call completed, drain pan safety switch open on arrival, removed water from dran pan , drain and flush condensation line, strongly recommended to replace air filter regularly, check system operations, unit is operating at this time , bill out account
Service call completed, safety switch open on arrival, drain line clogged removed heavily algae from drain pan , add drain treatment and check system operations, advised tenant to replaced air filter regularly, drain system is operating properly at this time , all systems vitals are good at this time
Unit had a failed dual run capacitor. Change capacitor and units fired right up. Compressor amp draw is 6.4/10.9 and fan amp draw is .35/.5
Cleaned indoor and outdoor coils as well as drain line and treated drain pan with antimicrobial agent. Checked all electrical connections and amp draws as well as refrigerant circuit pressures and temperatures. Unit is working fine. Customer should treat around unit with ant killer due to infestation. Not a problem now but can cause problems down the line.
No one home
Service call completed, upon arrival check with tenant to verify what kind of noises and were are coming from. Tested system to recreate any abnormal sound ,check electrical components and refrigerant pressure, during diagnostic noticed dual capacitor tested above the normal specifications , replaced defective components and re tested equipment, system is operating well and normal at this time, recommended to scheduled a system tune up
Service call completed, upon arrival check system operations and found thermostat wired incorrectly , unit is a heat pump and was wired for a conventional straight cool system, rewiring and change the thermostat operating system, during diagnostic found the condenser coil extremely impacted , coils in that condition can is causing the system head pressure to over heat the compressor, unit is way past the life expectancy, property was abandoned according to the office administrator, at this moment system is cooling but not work properly with the heat of the summer, send system replacement quote on the email on file , call office to schedule a system replacement
Cleaned indoor and outdoor coils as well as drain line. Checked all electrical connections and amp draws as well as refrigerant circuit pressures and temperatures. Unit is working fine.
Install April 26th and 27th
yearly tune up completed, drain and flush condensation, clean condenser coil and evap coil, check and tested system operations, all systems vital are good at this time
Yearly tune up completed, clean condenser coil and evap coil, drain and flush condensation line, check system operations, all systems vital are good at this
Service call completed, fix and sealed package duct work , tested equipment, all system vital are good at this time
Performed checkup and cleaning on Bryant Heat pump package unit for service contract customer