We were more than pleased with the service we received from Dave Taylor and Bay Area. The repair was made quickly and at a reasonable price. We would definitely recommend Bay Area to others.
Technician was very professional and fixed the issue quickly.
bay area is the best! All your techs are top notch.
Woke up to cold house on Sunday morning. Called bay area A/C Robert arrived within 2 hours. Had heat within 15 min. Heat very important to senior's. Thanks Robert.
The technician arrived as promised, explained what he needed to do, and did it.
service person was super
Service call completed, upon arrival check system operations and found thermostat wired incorrectly , unit is a heat pump and was wired for a conventional straight cool system, rewiring and change the thermostat operating system, during diagnostic found the condenser coil extremely impacted , coils in that condition can is causing the system head pressure to over heat the compressor, unit is way past the life expectancy, property was abandoned according to the office administrator, at this moment system is cooling but not work properly with the heat of the summer, send system replacement quote on the email on file , call office to schedule a system replacement
Cleaned indoor and outdoor coils as well as drain line. Checked all electrical connections and amp draws as well as refrigerant circuit pressures and temperatures. Unit is working fine.
Install April 26th and 27th
yearly tune up completed, drain and flush condensation, clean condenser coil and evap coil, check and tested system operations, all systems vital are good at this time
Yearly tune up completed, clean condenser coil and evap coil, drain and flush condensation line, check system operations, all systems vital are good at this
Service call completed, fix and sealed package duct work , tested equipment, all system vital are good at this time
Performed checkup and cleaning on Bryant Heat pump package unit for service contract customer
Repair electrical wires in a coalmine package unit for one of her main valuable customers and Homosassa Florida
Ordered module for blower motor on Heil heat pump package unit
Checkup and cleaning on Carrier 2 stage heat pump
Checkup and cleaning on Carrier heat pump package unit
ANNUAL AC MAINTENANCE TUNE UP AND CLEANING ON A 3.5 TON RHEEM HEAT PUMP SYSTEM.
AC SERVICE REPAIR ON A 5 TON TRANE STRAIGHT COOL COMMERCIAL UNIT. REPLACED CONTACTOR
AC SERVICE ON A 3 TON CARRIER HEAT PUMP PACKAGE UNIT. ORDERED BLOWER MOTOR AND MODULE.
AC SERVICE REPAIR ON a 3 TON RHEEM HEAT PUMP SYSTEM. Ordered new compressor.