Mike Barry is polite and on time. He did a great job. Thank you.
Thomas was right on time arriving at 8 am and completed all maintenance tasks in a very professional manner. Both our systems are functioning like new
The office called this morning for my annual service. She had an opening today and the tech was here within an hour!
Serviceman was punctual, courteous and went right to the problem and corrected it. We are very pleased.
Love Bay Area
Mike was very professional and stuck with the problem until it was identified. He took the time to fully evaluate all potentials and worked with the Carrier service line to identify the cause of my problem. The part is ordered and will be installed and set up shortly thereafter.
A/C wnt out early evening, called Bay Area and they had someone out before 9 pm. I was happy even if I had to wait until next morning for relief.
Yearly maintenance on a curator split heat pump for one of our many valuable contract customers and Lecanto Florida
Checkup and cleaning on Carrier heat pump
Replaced bad compressor evacuate and recharge system discovered bad expansion valve remove refrigerant replace the expansion valve evacuate recharge and test system. Heating and Cooling operating normal
A/C Service on Carrier 2 1/2 ton air conditioner. Performed preventive maintenance.
Annual check-up 3-ton Carrier heat pump
Lecanto Performed annual tune up on Carrier ac unit.
Annual check-up 5-ton Carrier heat pump
Annual service contract customer
A/C Service on Lennox 4 ton air conditioner. Performed preventive maintenance.
A/C Service on 4 ton Carrier air conditioner. Performed preventive maintenance.
Lecanto Performed annual tune up on Carrier ac system
Checkup and cleaning complete on Lennox heat pump and replaced thermostat
Maintenance on a 3-ton Carrier heat pump system
Lecanto Replaced t-stat on Payne ac system.