Jeff was very professional and informative. He even informed me of a duct service that could be the cause of plaster dust and eliminating it, which I am going to have done. He also gave me estimates on replacement a/c system for next year. He solved my overflow of the condensation problem which was the reason for the service.
the 3rd tech I've had come out and everyone was exceptionable. I knew nothing about Bay Area so I took a chance since my experience with Acree was a nightmare. As you can imagine, I had some trepidations, but I was pleasantly surprised and greatly satisfied with my choice.
Technican quickly found out what was wrong and repaired it/ .
Service Specialist Glen Holsapple made quick work of the inoperative AC unit today. Within 2 minutes of arrival, he was up on a ladder and had the problem isolated. Like the pro he is, he restored the unit to working order and was wrapped up and gone in 30 minutes. He took the time to explain how to avoid this same issue in the future.
I purchased my Carrier Air conditioner and handler from Bay Area Heating and Air Conditioning in Spring 2014. The system has keep the house cool and most importantly, my electric bill has been reduced substantially. I always have my annual maintenance done by Bay Area Air. This year, David, the technician diagnosed a potential problem with a part and replaced it. He was exceptionally polite and thorough in his work. It was a pleasure to have him service the unit.
I have some very bad experiences with other a/c companies, one of which resulted in me purchasing a unit for a lot more than I should have. It is a great relief to find a a/c company that I have total faith in, even after only two visits. Wish I would have found you earlier, would have saved me a lot of money and frustration.
Glenn always does a thorough and outstanding job.
If i need servive again i can only hope that i get the same tec i had today. This gentleman knows what he is doing. He is a professional.
Check thermostat on Carrier performance air conditioning system in Lutz
AC SERVICE REPAIR ON A 3 TON GOODMAN HEAT PUMP SYSTEM. CLEARED CONDENSATION DRAIN LINE.
AC SERVICE REPAIR ON A CARRIER HEAT PUMP performance system . Repaired TXV
AC SERVICE REPAIR ON A 3 TON CARRIER HEAT PUMP SYSTEM. REPLACED TXV
AC SERVICE REPAIR ON A 3 TON PAYNE HEAT PUMP PACKAGE UNIT. ADJUSTED REFRIGERANT CHARGE.
AC SERVICE REPAIR ON A 3 TON CARRIER HEAT PUMP SYSTEM. CLEARED CONDENSATION DRAIN LINE.
AC SERVICE REPAIR ON A 3 TON CARRIER INFINITY HEAT PUMP SYSTEM. REPLACED BLOWER MOTOR AND MODULE.
AC SERVICE REPAIR ON A 3 TON CARRIER PERFORMANCE HEAT PUMP SYSTEM. ORDERED TXV.
Replace indoor fan motor and outdoor circuit board Carrier Infinity system
Adjusted refrigerant on Carrier AC system
Blower motor replacement and quote for new system.
Service call for Carrier AC system customer
Carrier system maintenance