Technicians were professional and trust worthy
Contact Tune Up Need RS for filter 10/11/21 replaced filter.
Spoke to Adam about his concerns and we are going to schedule is maintenance inspection.
System out of freon R22 3 ton system holds 6.5 lbs $462 to add R22 If system changed out need to wrap a couple boo/s add return box. Gave quote on new system
no refrigerant in system Immediately located hole in suction line (arc burnt hole from rubbed thru hivoltage C wire) Repaired leak, pressure tested, evacuated & recharged Repaired wire & secured with wire ties
sending quote for Heat Pump system. Mini split . I messed up and gave customer price for A/C only.
No heat. Diagnosed both relays not engaging , and 1 limit switch tripped and not resetting. Recommend both relay and limit switch be replaced. System down
System got wet on inside and is sweating. Customer cleaned drain and is going to run fan on the on position until I get there on Thursday. Between 9 and 11. Going to give estimate to reroute drain because it keeps backing up causing this problem.
AC SERVICE REPAIR ON A 3 TON GOODMAN HEAT PUMP SYSTEM. CLEARED CONDENSATION DRAIN LINE.
AC SERVICE REPAIR ON A 5 TON CARRIER INFINITY HEAT PUMP SYSTEM. INSTALLED NEW CONTROLLER
AC SERVICE ON A 4 TON TRANE HEAT PUMP SYSTEM. GAVE A FREE SECOND OPINION AND FOUND NOTHING WRONG.
Replaced tstat on carrier infinity hvac heat pump air conditioning system in Brooksville
Repair low voltage wiring on air conditioning in Masaryktown
Annual ac tune up and cleaning on a Carrier heat pump system.
Replaced capacitor on a Rheem straight cool system