I'e been dealing with Bay Area for 23 years now. Always well pleased with their service and prices. Never had a problem with a repair. Good, solid business. When the founder sold out some years ago, I was afraid service might suffer, but from my perspective, that has not happened. It's like the original owners were still in charge.
Shane was very professional and Courteous.
You have been servicing our A/C for the past 14yrs.on more. Plus in between then you installed a brand new system. We even had you do the Aero seal on our previous house. Back then we had major leaks totaling to about %25 between supply and return air. After then it was reduced down to about %2. Yes we did feel the difference in the house, and in our pocket. Great service, and friendly knowledgeable techs.
Top quality service across the board.
Shane was very thorough and did a great job!!!!
Had excellent service for annual visit today. Service technician was very knowledgable and helpful.
Had to have service late yesterday afternoon. Technician arrived and solved the problem. Cannot say enough nice things about how well the job was done, Thanks!
$3400 for new ducts .
Install March 3rd
Annual check up 3-ton carrier heat pump
A/C Service on 2 1/2 ton air conditioner.Performed preventive maintenance.
A/C Service on Carrier 3 ton air conditioner. Performed preventive maintenance.
A/C Service on Carrier 4 ton air conditioner. Replaced indoor fan motor and verified proper operation.
A/C Service on Carrier 2 ton air conditioner. Performed preventive maintenance.
A/C Service on Carrier 3 ton air conditioner. Replaced indoor fan motor and verified proper operation.
Ocala Checked Carrier zoning ac system.
Annual check-up 3-ton Carrier heat pump
Ocala Replaced the blower motor on Carrier ac system.
Ocala Performed annual checkup on Carrier ac system.
A/C Service on 2 1/2 ton air conditioner. Verified proper operation of sysyem.
A/C Service on Carrier 2 1/2 ton air conditioner. Checked system and verified proper operation.
A/C Service on Carrier 3 ton air conditioner. Installed condensate pump and verified proper operation.