Jeff Wood Was very experienced and did a phenomenal job
The service personnel was fantastic.
Prompt, courteous, informative
Tech was knowledgeable and on time ..
We were very happy with our service professional. Thank you!
Perform yearly maintenance checks and cleanings. System operating at this time. Paid with #145374225
Perform yearly maintenance checks and cleanings for both system. System operating and draining at this time.
Wasn't able to remove the old line set. Rediagnosed the system to find that the copper line set and evaporator coil has no leak at all. Leaving pressures 158 / 325 21 degree superheat 2 year bay area labor warranty.
Spoke with Mrs. Hill and Mrs. Knight Mrs. Hill will need a separate invoice to bill job on a CC as she is making a percentage of the job cost to Mrs. Knight
System copper has been isolated and nitro tested by others Quoting 1890.00 to replace 2 sets of lines (4) understand thru a 4" pvc chase Homeowner would need a plumber to remove/reinstall the HW Tank And a plasterer to repair any damaged sheet rock (Bay Area not responsible to repair holes necessary to accomplish work)
Found drain backed up. Cleaned, flushed and treated drain. System now draining properly. System cooling
Upon arrival the plenum was leaking. I found big hole in plenum letting cold mix with warm air. This caused airhandler to sweat. I ordered a piece of duct board and come back to repair. Showed homeowner the hole and explained the repair to her.
2nd unit upstairs
Perform yearly maintenance checks and cleanings for 2 units. Replaced dual capacitor for upstairs unit. Both units cooling and draining at this time. #2 , invoice #142070163.
Cleaned drain major clog
Fou d failed dual run capacitor. Replaced capacitor no charge per 475. Capacitor slipped through and not changed at time of install.
Upon arrival found compressor not running. Located shorted dual run capacitor. Replaced capacitor and restarted cooling. Checked refrigerant level 40+5 dual run capacitor.
Found that the interior duct work is leaking air within the walls of the manufactured home.the vents are condensating.
Found defrost board not sending voltage to run fan motor. Bypassed defrost board to get system working.. Cost to replace board is $540. Customer is going to wait on repair at this time.