Cliff was prompt and extremely knowledgeable and educational.
Jeff is an asset to your company.
Marc was very knowledgeable, showed us and explained things as he worked through the problem and he was fast. Excellent service.
would definitely recommend them.
You could tell that Glenn has been in this business for a long time !!! He was very knowledgeable and thorough!!! Great job !!!
Confirmed small refrigerant leak at filter drier Need to RS for repair
This is An Estimate to Install A New Carrier 16 seer Two Stage Heat Pump.
Annual service contract tuneup and cleaning. I checked refrigerant pressures and static pressure. I checked all amp draws. I checked temp splits. I checked capacitor and contactor. I removed leaves from condenser. I waxed outdoor unit and cleaned both coils. I flushed drainline multiple times. I did not find any issues at this time. Reset UID for homeowner
System off on float switch safety. Recall. Cleaned out blocked condensate drain line. Added drain tablets and viper pan spray. Restarted and tested drain line
Found the system frozen over. Removed the impacted air filter and Deiced the systen. Will need to return tomorrow to add the freon.
Found float safety switch laying out of cup in open position. Reinsert float switch, all operating properly
Annual maintenance Customer provided filters All functions and operations were normal and within parameters withexception of drain safety float, quoted new (144.00) Due to age and conditions provided estimate fornew equipment
System 24 volt fuse was shorting out repeatedly. Traced short in 24 volt circuit to wire between air handler and outdoor unit. Pulled new wire and put original thermostat back on wall. Restarted and tested cooling.
One year parts and labor warranty.
Found drain only dripping when I arrived. Plugged drain and filled with drain solve. After several minutes I took cap off and allowed it to drain into bucket. Got a good bit of calcium out of line. I then ran a gallon of very hot water through drain. Got slime out of drain. Then with garden hose I flushed drain for several minutes and got more calcium and slime out of drain. Put some more drain solve in and washed it out with 2 gallons of water. Then treated with viper. Note: Took pictures of drain line in case this didn't solve the problem. If it didn't then we will likely need to replace drain line. Water was flowing good at this time
Found a shorted compressor. The system is 11 years old and out of warranty. Recommend replacement.
Found failed blower motor/module. Verified 240vac an 24vac to control module. Need new motor, customer is down
Annual maintenance with a new UV Bulb Found dual capacitor weak on fan circut, Replaced & tested
Compressor off on high temperature. Cool compressor and restart, compressor valve failure. Running but not pumping refrigerant. Recommend replacing system. Quote new equipment.