Upon arrival water was dripping under metal stand in closet. I opened panel and found iced over. I thawed system out by using heat mode off and on. Then I cleaned pan and condensation pump. While doing so I noticed outdoor unit jot shutting down. I found contactor stuck in. The contact was tilted and not making full contact and binding. I straightened it and worked fine. The system is cooling and draining into condensation pump and is pumped outside.