Representative arrived shortly after call was placed and fixed the problem very quickly and efficiently.
The technician, Keith, was very thorough, pleasant, and helpful with explanations of the service he provided.
Very happy with the service department and the amount of time that I was down was minimal. Thanks to all.
Wonderful job always !!!
You can tell "Carrier" that there touch thermostat is junk and almost useless. This new system does not work as good as the older system that it replaced.
Checkup and cleaning complete on Goodman heat pump
Replace water pump on hot water Recovery Unit connected to a 4-ton Carrier split heat pump for one of our many valuable contract customers in Beverly Hills Florida
Testing check hot water recovery unit for one of her many valuable contract customers in Pine Ridge Florida
Annual check-up 3-ton Carrier heat pump
Replace evaporator fan motor and a three-and-a-half ton Payne AC system
Beverly Hills Replaced blower motor on Carrier ac system
Check system adjust charge Rheem 2 ton heat pump
Beverly Hills Checked Carrier ac unit
Air conditioning repair 5 ton Trane heat pump drain line drain pan
Beverly Hills Replaced float switch on Carrier ac system
Annual check-up 3-ton Carrier Infinity system service contract sold
Annual check-up 3 ton Carrier heat pump UV bulb
Beverly Hills Replaced bad condenser capacitor on Carrier ac unit
Air conditioning repair 3 ton Carrier heat pump TXV x13 module filter drier thermostat
Beverly Hills Performed yearly tune up on Carrier ac system