The service was prompt and resolved the issue, I would give the serviceman 5 stars, but the labor charge was quite high for the work done, especially when added on to the service call charge.
Very thorough. Explained everything.
Representative arrived shortly after call was placed and fixed the problem very quickly and efficiently.
The technician, Keith, was very thorough, pleasant, and helpful with explanations of the service he provided.
Very happy with the service department and the amount of time that I was down was minimal. Thanks to all.
Wonderful job always !!!
You can tell "Carrier" that there touch thermostat is junk and almost useless. This new system does not work as good as the older system that it replaced.
A/C Service on Carrier 5 ton air conditioner. Performed preventive maintenance.
A/C Service on Carrier 3 ton air conditioner. Cleared clogged condensate drain line and added treatment to pan and line. Verified proper draining.
Air conditioning repair 4 tan climatemaster water source unit repair insulation on drain line
Annual check-up 4-ton Carrier heat pump
Beverly Hills Replaced bad condenser capacitor on Carrier ac unit
Replace blower motor and module on high efficiency Goodman check system and flush drain heat pump operating normal
Annual service clean coil and pan flush drain. Check charge and adjust outside drainage
Beverly Hills Checked TRANE indoor unit for water leak.
Deliver air filter for a 3-ton Carrier heat pump system and check drainage system
Air conditioning repair 4-ton Carrier heat pump refrigerant r410a
Beverly Hills Replaced Carrier air handler control board.
Annual service replaced UV bulb and weak capacitor operates normal
Annual check-up create a half ton Carrier heat pump
Air conditioning repair 3 ton Carrier heat pump TXV valve and filter
Checked out 15 year old Carrier Infinity heat pump