Representative arrived shortly after call was placed and fixed the problem very quickly and efficiently.
The technician, Keith, was very thorough, pleasant, and helpful with explanations of the service he provided.
Very happy with the service department and the amount of time that I was down was minimal. Thanks to all.
Wonderful job always !!!
You can tell "Carrier" that there touch thermostat is junk and almost useless. This new system does not work as good as the older system that it replaced.
Beverly Hills Cleaned up clogged drain on TEMPSTAR ac system
Yearly maintenance on a 4-ton Carrier split heat pump for one of our many valuable warranty customer in Beverly Hills Florida
Beverly Hills Performed annual tune up on Payne ac system
Replace low voltage control fuse with new checking for shorts in 4 ton Carrier heat pump system
Intertherm pkg system clean and service
Service Carrier infinity heat pump
A/C Service on Janitrol 3 1/2 ton air conditioner. Adjusted refrigerant charge and verified proper operation.
AC diagnosis 3 ton Trane heat pump
Air conditioning repair 3 ton Infinity system capacitor
Annual service found cracked drain pan adjusted thermostat from programmable to non programmable
Air conditioning repair 4 ton Infinity system thermostat
Maintenance Carrier Air
Annual check-up three and a half ton Carrier heat pump
Beverly Hills Performed yearly tune up on TRANE ac system
AC repair 2 ton Goodman heat pump low on refrigerant