We're new to the area so we used Bay Area because they were the ones who installed the new AC in our house before we bought it. So far they have been helpful, professional and quick to respond.
22.5 SEER 10 YEAR PARTS AND 1 YEAR LABOR WARRANTY
Installed 12 inch jumper duct from main trunk line to mixing box and relocated original jumper duct further down on main trunk to achieve more airflow to three doctors offices that were previously getting no airflow at all. Also added dampers to two supply vents in waiting area to be able to control airflow. Disconnected supply vent near thermostat and capped Warranty
Specific complaint of 3 office sized rooms by comparison to reception area Noted the center rooms flex duct was cinched with a duct tie (removed) Noted further exasperating condition is the thermostat is within 4' of a supply vent. Noted the reception area vents have much more velocity than the 3 rooms in question Will discuss results with Jim H.
Arrived at 1245pm to eat inspector to provide 8ft ladder. Inspector didn't show up until 215pm. Inspector passed job but breaker needs to be changed to 40 amp. See pic
Added some boot rails and put the exhaust fan in position. Added the cover and uploaded a photo.
Checking sound level of condensing unit