Our service provider was wonderful- not only doing the servicing needed but also giving us an education about the filters for our system. We really appreciate that!
The whole process with Bay Area Air Conditioning was a pleasure. Very straight, open and fair price quoting from their sales person Jim Horton; and awesome team of technicians led by Mark who were very knowledgeable and did a perfect install. I highly recommend Bay Area air conditioning.
We called for service and was thrilled to learn that they would be able to send a technician out the same day. The technician arrived earlier than expected and notified us when he was on his way. He was so professional, incredibly knowledgeable and nice and was able to resolve our issue promptly. We can’t express what a great experience it was to work with Bay Area Heating and Air and feel they are a service you can truly trust!
Your company employees show up on time, they are well mannered and trustworthy as well. They are quick and to the point and I don't feel any distrust in what they tell me is wrong. They always fix it and they never overcharge. I am so happy we found your company. We will never call another company to work on our air conditioners. Thank you for being an excellent company.
There is a reason I have used Bay Area A/C for over 25 years. They have always been consistent, professional, punctual and reliable. I would highly recommend them (angry have) to friends & family.
From prior service, checked ducting for sweating and or dampness, noted all prior ducting that was sweating (except 1) are now dry, added strapping to several ducts adjacent the supply plenum (especially the sweating one) to allow best attic air circulation and to separate ducting from "touching" each other
located several supply ducts in attic which are sweating Sealed hole behind wall controller and made some minor changes to air speed Recheck ducting in 2 weeks on a RS for the Tune Up
System cleaning and tune up
Completed the maintenance inspection
Acquired serial # for Parts / also model #
system confirmed low refrigerant Leak searched, positive hits several times at evaporator coil Advised Customer, Per Customer topped off charge Office to quote evaporator with extras
Found blower luckily stuck in on position at moment no matter if there is a call for heat , cool , or off. Need new motor and module. Possibly has a part warranty. Not one of our installations. Note has heating at this time also customer to be billed
Replaced 5 kw heat package with broken terminal block. Restarted and tested cooling.
Need to return with correct heater sticker and unit 1 and 2 labels for inside and out
Upon arrival the humidity was higher than set point for cool. The overcool function was disabled but fan would kick on to dehumidify but no compresser so fan only blowing wascausing humidity to rise. I explained to homeowner that system will cool 2 degrees below set point. I all went to condenser and the unit was very loud and vibrating. The blade looked as if it was out of balance. I ordered new blade and motor in case motor is damaged as well.
16 SEER 10 YEAR PARTS AND 1 YEAR LABOR
Found the system a little low on r22. Adjusted the superheated from 31 to 14degrees. 64 degrees coming from the supply vent. Vacuumed the drain system. No charge. Customer is having a new system installed on 9/30/2020
16 SEER 10 year parts and 1 year labor warranty proposal includes surge Suppressor at the condensing unit
Rewired thermostat and replaced weak run capacitor in outdoors Noticed that outdoor unit is R22 freon and indoor unit is designed to use 410a refrigerant. This is not the best match. Customer will call in payment
AC SERVICE REPAIR ON A 4 TON CARRIER HEAT PUMP SYSTEM. INSTALLED NEW FLOAT SWITCH