Drain fitting concealed in wall has come loose Accessed wall next to indoor unit and glued in new fittings Bay Area not responsible for wall repair
First floor main house system. Unable to run system at this time. Outdoor defrosted board is tripping 24 volt fuse. Defrost board will need to be replaced. Cost is pending. Thermostat has also been damaged by leaking batteries. Will also need to be replaced. Will need to be a two stage Thermostat such as the TCNHP by Carrier $312. This is a standard non programming thermostat. Collecting $97 for dispatch and time on main house system and additional $90 for checking other three systems. Total $187.
Second floor system 2 ton straight cool system System performance check will collect $30 on last invoice This system is the oldest system 2003 and uses R22 freon that is being phased out of production. Found no issues at this time.
Master bedroom system. Checking system performance. 1.5 ton straight cool system. Will collect $30 on last invoice. Found no issues with system today.
Inspection of Office system. 1.5 ton straight cool system Will collect on last invoice $30. Found no issues with system at this time.
Testing all functions on a new install put in last month.