Mark always does his job very professionally
Mark and Bay Area are outstanding. Great experience.
Professional, good sevice
Marc was knowledgeable, personal and quick to the rescue!
They get the job done quickly, very nice techs
Had an outstanding experience with Bay Area Air and would highly recommend them to anyone. Every step of the process was handled in a professional and friendly manner. Could not have been more impressed!
System cleaning and tune up. Replace Infinity air purifier filter and 2 uv bulbs.
Sytem maintenance on heatpump system. Second of two systems. Replaced filters in both. Colleting for all on this invoive.
System maintenance on heatpump system. One of two systems will collect on second invoice.
Discussed proposed duct modifications. Run jumper from supply plenum to distribution box at rear of home feeding exercise area. Run additional return duct to new distribution box. Returns daisy chained to main return remove and cap, reinstall 3 existing smaller returns to new distribution box.
Spoke with Ray about the duct modification. Marc was the technician work in my this deal with the customer. I will call Marc and update him. (Customer wanted to make sure we dealt with the return noise/air flow)
Quote to replace current defective plenum with properly sized 4ft supply plenum to allow room for future duct modification. Includes new 14" collars and reconnection of (2) 14" flex runs.
Found an indoor communication fault due to a bad indoor control board. The board was just replaced on 12/1/2020. Warranty no charge.
System running when arrived, found code 83, low pressure lock out in history for today. Checked charge as best as can (52f od temp). System low on charge. Need to schedule recheck and possible leak search on warmer day.
Site survey for duct modification.
EM Can't communicate with ID unit. Diagnosed bad control board at AH. Ordered new board. System down.
Dugdrainout and flushed system.
flush mount boxes needed & various fastners (home is CB construction)
blower motor and module
Found blower motor and module bad on the Trane air handler. To fix will need a new motor and module. System is out of warranty. Harry is going to call with quote for OEM part so customer can decide what motor they prefer.
System cleaning and tune up