Since we started using Bay Area Airconditioning New Port Richer we never, ever had Amy bad experience with them. Amazing customer service, amazing technician, awesome prices. They are always nice, professional and fast. Thank you so much for always helping us. Special thanks to the technician, he really deserve a raise $ ;)
Glen Knew exactly what needed to be done and took care of everything in a timely manner.
Arrived as scheduled and performed the service effectively and efficiently.
Glen is top notch air conditioner service representative. I hope Bay Area will continue to send him to house when I need service..
completed the maintenance inspection.
Completed the maintenance inspection.
Remove temporary wiring bypass. Check system operation.
Scheduled call for Friday
Found thermostat configured for gas furnace instead of heat pump. Cust said has not touched thermostat. Reset configuration for correct equipment and then cycled power. Thermostat will not retain settings. Need replacement thermostat.
Completed the virtual county inspection. County passed the install.
Found 30 amp breaker tripped to OD Unit. Reset system and tested amps are good . Compressor, and fan now working properly. Can't find any damage at this time. Possible surge or likely . System calls for a 40 amp breaker. Change breaker to proper size. Breaker that was marked for unit is a 40 amp but the one for this unit is below it. System is working properly at this time Warranty
Replace electronic float switch with manual float switch on Carrier gas performance air conditioning system in Wesley chapel
Carrier system maintenance
Maintenance check for our Carrier AC system customer
New Carrier AC system customer
Blower wheel replacement
Service call for Carrier AC system customer
Cleaned out clogged drain line on Carrier AC system