Jeff Wood was very thorough in explaining what was wrong and what he felt was necessary to repair the downstairs unit. He also advised what the cost would be prior to performing any work. The upstairs unit was also assessed and he indicated in was in perfect operation. That was honest and so appreciated. We’ve had our share of poor service in the past. Plan on calling Bay Area Air Conditioning in the future. Thanks again Jeff.
Jeff is very knowledgeable and took time to explain the problems with our unit and what he wanted to do to repair the system, along with pricing. I can’t tell you how refreshing this experience was as we have had our share of poor service in the past. Thank you Jeff and Bay Area Air Conditioning.
Since we started using Bay Area Airconditioning New Port Richer we never, ever had Amy bad experience with them. Amazing customer service, amazing technician, awesome prices. They are always nice, professional and fast. Thank you so much for always helping us. Special thanks to the technician, he really deserve a raise $ ;)
Glen Knew exactly what needed to be done and took care of everything in a timely manner.
Arrived as scheduled and performed the service effectively and efficiently.
Glen is top notch air conditioner service representative. I hope Bay Area will continue to send him to house when I need service..
Upstairs 3 ton HP. Check system operation, unit is in good working condition. 22* TD at supply plenum. 9* SC. Charges applied to #139208848
Downstairs unit, 3 ton HP. Check system operation, replaced dual capacitor in OD unit. Recover 1 lb R410A from system. SC now at 12*, was at 22*. 54* at supply plenum. System operating and draining at this time.
Customer called our office and canceled NOTED: Called customer prior to dispatching, during call the Mrs. had stated they just had a maintenance about a month ago from another company.
Check system operation, low refrigerant, advise customer of age and condition of system and Recommend replacing system. Customer declined. Quote new equipment.
completed the maintenance inspection.
Completed the maintenance inspection.
Remove temporary wiring bypass. Check system operation.
Scheduled call for Friday
Found thermostat configured for gas furnace instead of heat pump. Cust said has not touched thermostat. Reset configuration for correct equipment and then cycled power. Thermostat will not retain settings. Need replacement thermostat.
Completed the virtual county inspection. County passed the install.
Found 30 amp breaker tripped to OD Unit. Reset system and tested amps are good . Compressor, and fan now working properly. Can't find any damage at this time. Possible surge or likely . System calls for a 40 amp breaker. Change breaker to proper size. Breaker that was marked for unit is a 40 amp but the one for this unit is below it. System is working properly at this time Warranty
Replace electronic float switch with manual float switch on Carrier gas performance air conditioning system in Wesley chapel
Carrier system maintenance
Maintenance check for our Carrier AC system customer