System has dirty evaporator coil, restricting dehumidification. Compressor amp draw is 8.9/18 and fan is .9/1.1. Filter was slightly dirty at time of arrival. P Trap was positioned in a way that it would allow air to be ducked in from outside and not dehumidify properly. Adjusted and printed p trap, cleaned coil, and instructed tenant to change filters more frequently. The mini split is operating fine. Pressures and temperature splits are normal and unit is cooling. If customer has issue with heat still, recommend adding fan to better circulate air, and possibly turn in exhaust fan in bathroom to remove warm air sitting near the ceiling.