We truly appreciated the great service we received from Jose Montes ... He spent time going over what he would be doing as well as offering us Bay Furnace Club Membership which we did sign up for and were very happy with the savings on our service call ... Thank you!!
I cannot say enough about all the wonderful service I have had over many years. Kim always is so helpful and Marty has always had my complete confidence in so many ways. Always explains everything and gets problems solved with his great knowledge and courteous manner. I can t imagine calling anywhere else. Thank you Kim and Marty for being there. I truly appreciate you both.
Jose did a great job of explaining things in layman's terms. Very prompt, efficient, and personable.
Very good service
Marty is a great technician and is always able to correctly identify the problem and knows how to get it fixed.
Our furnace (put in by a flipper) was only two years old when it started to malfunction. Bay came in and worked overtime to get replacement parts, we ultimately replaced the whole unit but I cannot imagine many companies spending as much time talking me through all the options and trying to find me the best products for the best price possible. I will sing their praises to the moon.
Jason was friendly and professional. He was well informed and I was very pleased with his service.
Thank you for all the support! From multiple options to replace old furnace, fitting into a expedited schedule, installation, to walkthrough of wireless thermostat. Great job Bay Furnace!
Brian was great; very professional.
Found pressure switch not opening. Remove and check. Also clear pressure switch tubes. Cycle to check ok.
$119.95 Furnace Tuneup. T-Stat, 50 Ohms HSI, Flame Sensor,90% Inducer, Electric, 3.5â€ W.C. Gas Valve, Drain Trap, Blower Motor, 33* Outside, Cycled Unit, Clean And Check. Ordering 90% Inducer On 1/21/2019.
Heating tune up and filter replacement.
$119.95 Furnace Tuneup. Replace HSI, #201Sg, #35Wp, 10+370 Run Cap. â€œFurnaceâ€ T-Stat, Flame Sensor, 2-Stage 80% Inducer, Electic, 1.5â€ & 3.5â€ W.C. Gas Valve, 33* Outside, â€œHumidifierâ€ Fan Power, Scale control Insert, Feed Tube And Nozzle, Water Valve, Solenoid, Drain Trap And Pump, Cycled Unit, Clean And Check.
Found 20 amp fuse blown in main electrical disconnect panel remove and replace with customer supplied cycled unit to check check amp draw all three phases of 460 V service 1.8 A under full load each leg cycle rooftop in heating to check OK.
Not sure how to work the humidifier. I explained the operation of the humidifier. I replaced the water panel. I cycled with proper operation.
$119.95 Furnace Tuneup. Replace #35Wp, Feed Tube, , Ez-Flex #24. â€œFurnaceâ€ 4= T-Stat, 52 Ohms HSI, Flame Sensor, 2= Stage 90% Inducer, Electric, 1.5â€ & 3.5â€ W.C. Gas Valve, Drain Trap, V.S. Blower, 33* Outside, â€œHumidifierâ€ Hum-Stat, Bypass Damper Open, Scale Control Insert, Water Valve, Cycled Clean And Check.
I found the flame sensor was reading .4 - .9 miliamps. I removed,cleaned and tested at 6-5.1 miliamps.
Commercial maintenance Replaced filters Checked burners, inducer, blower. Checked tension on blower belt. Ok
$119.95 Furnace Tuneup. â€œFurnaceâ€ T-Stat, 78 Ohms HSI, Flame Sensor, 90% Inducer, Electrical, 3.5â€ W.C. Gas Valve, Drain Trap, #201Sg, Blower Motor, 33* Outside, â€œHumidifierâ€ Hum-Stat, Fan Power, Water Valve, Electical, Solenoid, Cycled Unit , Clean And Check.
Com furnace maintenance Changed filters, cleaned burners, checked inducer and blower. Checked blower belt, ok.
Found condensate drain line clogged remove plug with vacuum cycle furnace and humidifier to check OK
Check furnace found filter plugged customer to replace airflow did increase to front bedroom but ductwork inadequacies exist with system furnace installed in 2018 by others but ductwork in adequate may need estimate on ductwork replacement in basement office will call to set up estimate
Furnace tuneup Changed air filter, customer provided. Checked igniter, flame sensor, burners, gas valve, blower, capacitor, safeties, controls, cabinet, trap, intake. Cycled from tstat, reset tstat.