The team showed up on time, did the correct work, and were very neat!
Found out Furnace Board has Pod's that need to be set properly, furnace will not go to second stage on its own
Everything went well with no complaints.
Furnace is not heating properly. I found the flame sensor was not reading any microamps upon arrival. I removed cleaned and retested at 2.1 Âµg. I cycled the furnace for 15 minutes with proper operation. I also replaced the filter with the customers supply. Coustomer could not print the coupon.
Upon arrival found the gas was not on to the house.
Found unit off on hi limit lock out. This is due to a dirty filter. After changing the filter and resetting the furnace system is operating properly at this time. Thanks Brian and Marty.
Found unit locked out due to open limit. Furnace had overheated due to dirty filter. Replaced filter and reset control board. Cycled system and system is operating properly at this time. Thanks Brian and Marty.
Found feed tube cracked, remove and replace, cycle to check, ok.
Found pressure rising too high Adjust water feed valve lower cycle boiler several times to check leaking from pressure relief stopped
Bypass infinity control with regular thermostat to get heat until tomorrow
upon arrival I found the noise they were hearing was from a water droplet falling onto the fan blade. I added a piece of plastic so the water would follow gravity down onto the water panel. The water was following the roof of the unit and dripping on the fan blade. After this adjustment was made the humidifier was cycled cycled for 20 minutes with no more noises.
We replaced 10=16x25x2 and 16=16x20x2 filters.
Upon arrival customer cycled system. Could not get system to repeat the noise that customer was explaining. Unfortunately we arrive later than 9 AM estimate. And customer has to leave for work right now. He will keep an ion it and try to record the noise when it happens.
Found blower motor failed after running for approximately three minutes. We tried a new capacitor which did not work. Customer does not want to repair at this time. We emailed 2 estimates and will wait to hear from him. System is not running at this time. Thanks Brian and marty
Furnace tuneup. Burner and blower compartments were inspected all safeties and connections were checked. Ignition sequence was cycled . Blower compartment and wheel were checked out. The system was cycled with proper operation. We replaced the filter with the customer supply. The furnace is in proper working order at this time.
Found bad ignitor. Replaced part. Cycled system and system is operating properly at this time. Thanks Brian.
Replace Part. Replace 90% Inducer Assembly, Cycled Unit Fine At This Time.