Knows what he is doing
Besham Basdeo came to our home for a tuneup on our furnace and air conditioner ... He was very thorough, explaining all he had done as well as suggesting something we may check into ... He is also a very nice person!! Thank you, Dana Kertes
Service was excellent, as always. Your technician was very professional
Jose was great. Thorough, quick and very knowledgeable!
He explained the options with a leak in the system and probable prices. I felt he leveled with me. Good man.
Johnathan arrived and promptly set out to work, being careful not to bring in outside dirt after this mornings rain. he promptly performed the service tune up indoors and then tackled the outdoor unit. He briefed me on his findings and gave me a few tips in the process.
Jason has been here a couple years ago when furnace broke Got us heat until new unit was installed. This time ac broke. Put in new part and quickly had ac again on very humild day. Hes also a nice guy.
electronic air cleaner was not working upon arrival. I disconnected Wire from power source. Unit is now not electronic air cleaner only a filter rack. Cycled system to check. System is operating properly at this time. Thanks Brian.
Club A/C Tuneup. Replace Bad 28+4.3+370 @ 35+5+370 Dual Run Cap, T-Stat, 72*-52*=20* D-T, Drain Trap, Blower Motor, R-22, Disconnect, 2=30 Amps Fuse, Electrical, 71* Outside, Hose Down, Remove Leaves And Cottonwood, Cycled Unit, Clean And Check.
Check thermostat check blower motor change filter customer supply flush condensate drain. Supply air 56* return air 70*. Check disconnect check capacitor 40+5+440. Cycle unit on to check compressor and fan motor working. Wash and clean condenser coil. Outdoor temperature is 70. At times of dispatch unit is working.
Unit one (upstairs) Check thermostat check blower motor check filter customer supply flush condensate drain. Supply air 60* return air 71*. Checked disconnect checked all electrical wires on vna Unit . Cycle unit on to check compressor and fan motor working. Wash and clean condenser coil. At time of dispatch unit is working. Unit 2 (downstairs) Check thermostat check blower motor check filter customer supply flush condenser drain. Supply air 52* return air 68*. Check disconnect check capacitor turbo run Cap. Cycle unit on to check compressor and fan motor working. Wash and clean condenser coil. At time of dispatch unit is workings. Outdoor temperature is 75*.
Air-conditioning tuneup. Customer also stated upon arrival that it did not seem to be cooling as well as it should be. I washed out the condenser coil. I checked the contactor and capacitor. The capacitor is reading 34 out of 35 ÂµF. I flushed out the condensate trap and check the media filter. I cycled the system and found that it was low on charge. I added 6 lbs. 8 oz. of refrigerant 410A. This brought the system to 11Â° of sub cooling. System is operating properly at this time. There is no warranty or guarantee for adding refrigerant . I found that the service valve caps were loose on the condenser. If leak reoccurs I recommend performing a leak search and making repairs to the system or adding a leak stop to the system.
Club A/C Tuneup. T-Stat, Ez-Flex #20, Drain Trap, 72*-56*=16* D-T, Blower Motor, R410A, Disconnect, 35+5+370 Dual Run Cap, Electrical, 77* Outside, Hose Down, Cycled Unit Clean And Check
Customer said unit is leaking. Pour water in condensate drain and found it was closed. Pressure it with air and then pour water. Can now hear water running out. At time of dispatch condensate drain is ok.
Replace 2 A/C'S
Water leaking. And tuneup. I found water leaking from the condensate trap. I flushed condensate trap with 8 L of warm water. I removed condensate pump and cleaned all the slime and sludge out of it. I flushed more water through it and system is not leaking at this time. I replaced the media filter. I cleaned the condenser coil. I checked the contactor capacitor and all connections. Capacitor is reading 45 x 5 ÂµF. I cycled the system with a 20Â° temperature drop. System is operating properly at this time.
Furnace And A/C Tuneup $119.95 Each. Replace Air Filter. Cycled 2-Stage Heating And 1-Stage Cooling, Fine At This Time. 77* Outside.
Checked thermostat. Flushed AC trap with water. Checked filter. Changed filter supplied by customer. Checked capacitor. Checked contactor. Checked all electrical connections. Cleaned outdoor condensing coil with water. Cycled system to check. System is operating properly at this time. Thanks Brian
After thoroughly inspecting the furnace I could not find the slight tingling rattling sound coming from inside the heat exchanger. I checked all screws and all exterior pieces of the furnace for vibration and could not find the source. I remove the induced draft motor and listened inside the furnace and I can hear a slight pinging almost like a screw is bouncing around down in there. The furnace is 18 years old and the amount of labor and the cost of finding the noise is not recommended due to age and condition of system. I gave 4 options on replacement. Thanks Brian.
I replaced the blower motor and cycled the motor with proper operation.