Jason was outstanding
Marty is the consummate service person for Bay Furnace. I always request him if available for my air conditioner / furnace annual inspections.
Did what was expected.
Tech was great found the issue to be a loose drain cap. Secured it and was on his way
Jose is professional and efficient. Always a positive experience.
Great service and awesome price
Found zone one to be powered by transformer either in attic or at zone control and was not hooked up correctly at installation of zone system install had to put both common wires under C of thermostat. thermostats were changed in September and not wired correctly from that point .
The problem lies with standing water and rust in the burner compartment. I found the water leak was from a backed up condensate drain for the air conditioning coil. I accessed the condensate trap cleared with high-pressure CO2 and flushed with 2 L of water. I cycled the air conditioner with a 21Â° temperature drop. System is in proper working order at this time.
Check thermostat check blower motor check filter customer supply. Cycle unit on to check compressor and fan motor working. Check capacitor 40+5+440 Dual Run Cap. Supply air 51* return air 69*. Wash and clean condenser coil. Outdoor temperature is 76*. At time of dispatch unit is working.
No cooling. I found a failed dual capacitor. I replaced it and cycled with proper operation. Upon further investigation I found the fan blade is cracked. I am providing a price to replace the blade and motor.
Club Furnace And Humidifier. Replace #12Wp. T-Stat, 60 Ohms HSI, Flame Sensor, 90% Inducer Assembly, 3.5â€ W.C. Gas Valve, Drain Trap, #20x25x5 Air Filter, Electrical, 76* Outside 10+370 Run Cap Blower Motor, â€œHumidifier â€œ Hum-Stat, Bypass Open, Water Valve, Solenoid, Feed Tube, Electrical, Drainline, Cycled Unit, Clean And Check.
Heating tune up. Replace filter and water panel. Gherkin garage heater and adjusted manifold gas pressure.
Club Furnace And Humidifier Tuneup. Replace #35Wp. T-Stat, Spark Igniter, Flame Sensor, 4+370 Run Cap 90% Inducer Assembly, 3.5â€ W.C Gas Valve, Burner, Drain Trap, 15+370 Run Cap Blower Motor, 71* Outside, â€œHumidifierâ€ Hum-Stat, Fan Power, Scale Control Insert, Water Valve, Solenoid, Feed Tube, Drainline, Cycled Units, Clean And Check.
Install class B pipe
Unit 1 Check thermostat check blower check humidifier change filter check hot service ignition 85 ohms. Cycle unit on to check all other components on unit. All others information please check heating Tuneup form. At time of dispatch unit is working. Outdoor temperature is 66* Unit 2 Check thermostat check blower change filter check hot service ignition 49 ohms. Cycle unit on to check all other components on unit. All other information please check heating Tuneup second unit form. At time of dispatch unit is working. Outdoor temperature is 66*.
Clean burners flame sensor condensate trap vestibule and controls change humidifier water panel and filter check all operating and safety controls fire furnace to check low and high fire
$119.95 Each Furnace And A/C Tuneup. Replace #413Sg. â€œFurnaceâ€ T-Stat, 50 Ohms HSI, Flame Sensor, 80% Inducer Assembly, 3.5â€ W.C. Gas Valve, Burner, 7.5+370 Run Cap Blower Motor, 64* Outside, â€œA/C Unitâ€ T-Stat, #413Sg, Drain Trap, 70*-50*=20* D-T, Disconnect, 2=40 Amps Fuse, Electrical, Hard Start & 45+5+440 Dual Run Cap, Hose Down, Remove Leaves And Cottonwood, R410A, Blower Motor, Cycled Both Unit, Clean And Check.
Unit Making Noise. Found 220 Line Reading 346 From Breaker Box, Owner Will Electric Company.
Water leaking. I cleaned the condensate trap with CO2.;I cycled with proper operation.
Club Furnace And Humidifier Tuneup. Replace #201Sg. Bypass Humidifier Not Used. T-Stat, 56 Ohms HSI, Flame Sensor, 2-Stage 90% Inducer Assembly, 1.5â€ & 3.5â€ W.C. Gas Valve, Drain Trap, Electrical, 132* & 122*-72*=60* & 50* T-R, V.S Blower Motor, 73* Outside, Cycled Unit, Clean And Check.