Took care of everything quickly and did a good job.
Diudonne was wonderful, did a thorough job and explained things along the way.
Eric did an excellent job correcting our plumbing issue. He was friendly, courteous, knowledgeable, efficient and did a wonderful job keeping everything clean. I think he went above and beyond in taking care of our issue.
Tech could not have been better, absolutely awesome! He went way above and beyond to make sure the AC worked during a family crisis we were soon to face.
Adam did a great job rerouting our sink line, explained everything including the capping of the old line. He was very courteous and left with the area cleaner than when he began the work
Levi gave our furnace its annual check-up. He was very friendly and efficient. He answered all our questions. I hope he comes back next year.
John was very nice and very informative. Would highly recommend him!!
Below is a summary of your new Bradford White 50 gallon water heater
Remove tube trap and discard. Furnish and install longer tailpiece connected to strainer. Furnish and install new tube trap with extension tailpiece. Two year labor and material warranty. Paid by card.
Found drain at evaporator loose, vacuumed out excess water, backed out, retapped and reinstalled. Checked Filter, folded over 20x20x1. Measured opening, found a 17x20x1 would fit. Customer stated during install old filter door was sealed off and new access was cut into return plenum and labeled 20x20x1.
Preform Fall Tune and Clean on Furnace Furnace Service Arvada Co
Customer supplied faucet install
Arvada, CO 80003 ac check
Arvada, CO 80003 Need electrician. Bad double 20 amp breaker
Brandon replaced 2â€™ of 1/2â€ copper 1 year parts and labor warranty
Diagnosed and confirmed refrigerant level and operation. 20 degree split of 64 to 84.
Membership, repair moen single handle tub/shower cartridge, inspection minor at second moen tub/shower valve needed it's handle replaced. New silver maintenance member. wear parts and labor warranty. Paid $953.00 by card.
Hose bib replacement
Need to replace shut off and prv
7/22/21 Dieudonne, I am here at the address above, Concern: customer requested ac tune up and check. See attached forms for tune up and check. Ac is working normally at this time. Total cost of the service today is $354 paid by check number 1012.
Disposal repair. Tech: Tomas.
Electrical service-Inspect the outlet box the outlet device and the wires and make sure that everything is in good shape by the burn marks on the box