Russ was fantastic!
Mark did a great job, friendly and courteous as well.
Tomas did a great job. Very informative and told me what needed to be done and why
Jordan was friendly and knowledgeable. He explained everything in a way I understood to get our house up to code.
The technician was excellent. My problems run deep and require a general contractor. The technician did everything possible to explain and give me prices. He did fix one small problem and the price was excellent.
Bell Plumbing and Heating is the most dependable company you can ever find for plumbing repairs, heating, air conditioning etc. They may not be the least expensive but they are the best at what they do and worth every penny spent on their services!!
Nice overall company
Nicholas and Frank did a great job. They were very helpful and answered all my questions. I would definitely highly recommend them.
As usual, service is top notch. I've been using Bell for several years. They don't do anything except the best way. It may cost a little more but I think the value is excellent.
Very Polite and professional
Customer had leak on saddle valve going to refrigerator. Replaced with a quarter inch compression ball valve
Castle pines - humidifer service
Job was turned over to Brad.
Customer had ball valve on sprinkler system that was leaking by. Head bleeder cap off and and water was landing on the floor. Installed new ball valve
Electrical service on porch light
Number one tank of two in series is leaking. Bypass this tank to have number two tank operate until replacements of both 50 gallon tanks or one 75 gallon tank with a mixing valve. Owner requests a proposal also for a recirc pump and up to three bypass valves installed to obtain hot water faster at certain locations. Scheduled with Linda to have Brad Garton out Monday, January 17 between 11 and 12 to provide a proposal. One year labor and material warranty on supplied material. Paid by card. See attached pictures for other suggestions.
Chris M and Josh W: came out due to customer hearing squealing/ whale sounds from the boiler when it would shut off. Started up unit with the basement thermostat turned all the way up and was able to recreate the sound. Sound was coming from the primary circulator pump when the secondary circulator pump would shut off. Adjusted bypass valve handle to allow more flow and prevent deadheading of primary pump when secondary pump shuts off. No charge due to recent installation of pump. This is a warranty call.
Castle Rock, CO 80109
Chris M came out due issues with boiler pump. Performed diagnostic. Found circulator is starting to die out. Gave customer option to replace. Got permission to replace. Replaced with brand new oem 00 e taco delta t pump. Made sure no leaks. Found no leaks. Next wired up sensors and tested delta t at 20 degrees. System is heating and operational at this time according to manufacture specifications. 2 years parts and labor warranty on all repairs made today. Customer paid in full on cc.
Met with Steve, looked at furnace, replaced two pvc fittings. Furnace Repair Castlerock CO Good Option
Chris Rosales came out due to no heat, upon arrival found gas valve appears to be sticking however cannot recreate problem. Customer is however dissatisfied with the performance of thermostat, quoted customer on. New gas valve, thermostat and glow igniter due to damaged state it may fail soon. Customer stated that he only wants the thermostat at this time. Furnace is past 15 years, recommend seeking replacement options as well and we can supply quote. Customer said he has a cleaning scheduled Friday and will address membership and gas valve the. Customer paid $498.00 on credit card. Unit is heating at this time.