Jim did a great and and clean job.
"Tune-Up" for HVAC provided in professional & efficient fashion.
Ben seemed to really care about doing a great job and he did it.
Replace the TXV, recover refrigerant, and nitrogen test.
Upon arrival, client had two toilets she wanted looked at. First was powder room toilet right at entry way. Toilet is old water closet, where tank is mounted up on wall. Unfortunately we do not repair a toilet this age. Gave options to replace. Second toilet was guest bathroom on main floor, toilet would occasionally run, put dye tablet in and found leak coming from flush valve gasket. Gave options to repair toilet. Client authorized me to replace shut off valve and do a major toilet rebuild. Shut water off and replaced straight 1/4 turn stop. New supply line, tank to bowl bolts, fill valve, and flush valve with flapper. Tested and everything working properly. 2 year warranty parts and labor.
Brandon replaced flapper in Toto toilet
Furnace and air conditioning system
Took pics of backflow and surrounding area per Denver Water. Tech: Tomas.
Cherry hills - inspection
6/18/21 Dieudonne, I am here at the address above, Concern: customer requested ac tune up on 2 units both in the attic. See attached forms for tune up and check. Both Acs are working normally at this time. Total cost of the service today is $488.50 paid by credit card.
Met with Greg and his wife, we discussed no ac issues. Had reduced cooling and they Changed filter and got cooling operating again. Discussed options and moved forward with 2 memberships for two systems,and I would inspect steam April aire 800 humidifier. Began checking both ac systems. Started in attic did full checklist found some small issues, corrected condenser with rinse down, at furnace and coil up stairs made some adjustments to dipswitches to maximize cooling and make system as efficient as possible. Also found txv mounted improperly very loose and not metering refrigerant correctly. Fixed issue tested again and pressures and temps corrected 9sh 110 sc 21 delta t. Basement system also needed adjusted was set to run 5ton of cooling on a 3 ton ac system adjust and verified same as attic system now running much more efficiently. Both systems used 20x25x1 filters. Steam humidifer needs new canister April aire canister #80. Ran thru cycles worked correctly but canister bad found lo
system not cooling
Chris Rosales came out due to no cool, this is a new installation. Customer said it has never worked. Upon arrival found transformer in indoor unit was bad. Changed out transformer, unit turned on and began to cool. Then turned off , the fast stat is either over apping or is too hot. May need to rewire with new thermostat wire, will need another tech to help. Derek should be scheduled to come tomorrow per customer to help fix new installation. Unit is not cooling at this time, NC warranty call
Took a picture of the backflow, per Denver Water, showing itâ€™s installed at least 12inch above ground level. Also, tested and certified the 3/4inch Febco RP backflow. Backflow Assembly Passed. Bell will submit the results to Denver Water. Total of $175.00 to be billed. Tech: Tomas Magallan.
Reduced pressure principal backflow assembly on irrigation system: small leak occurring at downstream union. Back off half of union, lubricate and retighten firmly to stop leak. Reinstall vandal cage. Continuation of original warranty.
Furnace check up for winter
Humidifier repair in Denver
Gas line repairs