Chris knew my system in and out. He was able to explain everything to me and was so polite and fun to talk with. I will always request him to service my heater, a/c and boiler units. Exceedingly happy with his professionalism.
Chris McQuistion came out due to needing to finish a job. Customer did not have another port for other gateway to hook up thermostats. Was able to hook up thermostats today and gateway. Tested everything properly. System is heating and operational at this time according to manufacture specifications. This is a continuation of previous job and not call back or warranty.
Fox field - boiler
Chris Rosales Came out due to no cool upon arrival found unit is off, turned unit on and system started too cool home. Recommend AC tune up, customer agreed. Found system is cooling at this time, condenser run cap is weak on fan side and AC coil has rust marks. Customer does not want to replace run capacitor at this time. Customer paid $354 with a credit card.
Chris McQuistion came out due to wanting safety and tune up performed on air conditioner. Performed the safety and tune up checklist provided with the service agreement plan. Found really low delta t of 15 degrees. Found very clogged outdoor coil where the jacket would need to be removed to be cleaned. Found contactor pitted and burned. Found capacitor is failing and rusting. Found condenser fan motor failing. Has oil dust around the outside which is signs of failing. Provided options for repair. Customer agrees to to peace of mind. Unfortunately I will have to order these components. Rescheduling customer for Wednesday between noon and 2 pm. Will collect full amount upon completion. Will need to get a 60/7.5 mfd capacitor with order. Chris McQuistion came back with components. Turned unit off. Took jacket off of condenser and cleaned thoroughly. Took condenser fan motor apart. Replaced with brand new fan motor. Replaced capacitor with brand new capacitor. Replaced contactor with brand
Boiler repair in aurora