Chris and the Bell team repiped our boiler after the original installer had done it all wrong. They explained the process and what was wrong, and proceeded to do a top notch job with follow up when a small problem arose. Not the most fun way to spend money, but we now have a boiler that heats the house and water.
Jon did a great job. I could tell the minute he introduced himself he was customer friendly.
A late day repair time turned into a morning time because of a cancellation. Chris was very pleasant to work with. A short greeting by Chris was followed by an explanation regarding his diagnosis of the problem. He was very knowledgeable and had our hot water heating system on track quickly. My thanks for a job well done, Chris.
Trip charge. Need boiler tech, had new boiler with side arm replaced by different company recently. And in order to maintain warranty need original tech.
Installed furnace and A.C. In Golden, CO
Installed new Furnace and A.C. In Golden, CO
Installed new A.C in golden, CO
Chris McQuistion came out due to issues with heating system. Found that the heating system is radiant heat. The zone valve has failed and needs to be cut out and replaced. Found that the thermostat has been misfired and possibly has failed due to this reason. Found that the face plate of the radiant heat in one of the bedrooms is completely missing. Gave customer options. Got permission to perform work.started by going and grabbing correct components. Came back with correct components. Isolated the water line heating loop inside home. Drained the system as much as possible. Cut out old zone valve. Added new zone valve. Tested for leaks. Found no leaks. Next tested wiring on thermostat and zone valve. Found thermostat is not calling for heat when asked to. Changed out thermostat to new thermostat. Programmed thermostat correctly. Tested and found system is functioning as should at this time. Next went to baseboard heating radiant in bedroom. Took apart old radiant heat backing and cover
Quote on new System
Installed Ecobee T stat. Will return after demo for furnace tune up. Consulted on vent block off. Decided not to do. A/C Service Golden Co
Chris Rosales came out due to no cool, customer stated the breaker is tripping. Recommended a tune up and condenser cleaning to start. Customer agreed, to membership and condenser cleaning. Condenser is still tripping breaker, performed 13 point inspection and found condenser is not receiving proper voltage. Only receiving 226 volt, condenser requires 240 volts. Recommend electrician to come out and check high voltage. Customer paid $565.35 on credit card. Unit is not cooling at this time.
Dishwasher and Disposal outlet repair
Ptrap was rotten and pouring water out of it. Replaced with pvc ptrap. Working great.
Golden, CO 80401 Ac check
Upon arrival, client had some faucets and toilets with very low/no water pressure on cold lines. Hot water is present in all points of use, and cold water in showers and kitchen faucet. Client said they had shut water off to home today, and different contractor had installed a tee and valve on main water line for sprinkler system. He said when they restored the water to home, this is when he issue started. Client authorized for inspection on all points of use that had no cold water. Shut cold water valves off, and removed supply line, flushed hot water through faucets and found flux from soldering, and what seemed to be bits of paper towel that may have been used to dry and stop dripping when soldering causing issues. Cleared debris from 4 faucets and got them working properly. Master bathroom toilet had very low pressure, cleared supply line with no improvement. Gave client option to replace fill valve, he authorized. Replaced fill valve for master bathroom toilet. Tested and everyth
I Customer had stub out for gas on the patio. Removed cap and installed 90 and shut off, reducer and quick connect for gas grill. 1 year warranty parts and labor. Also educated customer on lighting fireplace.
50 gal water heater replacement
Golden mini split - noise issue