On time and efficient.
Roke is the best! Very knowledgeable and very thorough. Came on time.
A very satisfied customer. Furnace was making sounds that it should not be. Very quick and accurate diagnosis.
From Brad who started the job, to Holly, Dan,Derek,Mark,Daniel, Fred, Josh and Joe. The experience was as wonderful as a sewer line replacement can be. They took very good care of our home. Keeping us posted on progress throughout the entire project. Thank you so much.
Water heater supply leak
Toilet auger Ran the motorized toilet auger with the 6ft extension and was able to clear obstruction. Flushed the toilet multiple times with no issue
Diagnosed evap coil leaking refrigerant. Lance to be scheduled to quote replacement. 500 credited towards estimate or replacement of air conditioner. 14x25x1.
Chris Rosales came out to flooding due to AC condensation leaking on the floor. Customer said she had flooding last week when it was really warm. Filter was dirty and frozen, blower wheel is clean and acoil is clean. Acoil is extremely rusty and more then likely has a leak in ACoil, rusted debris has fallen into Acoil pan causing it to not drain properly and leak down the sides. Recommend replacement of Acoil, pee trap, condensation line, adding a TXV and overflow switch. Customer would prefer to get a new system rather then replace coil. Customer paid trip $49.00 and set up lance to come out for quote.
Prior to arrival, Margaret had noticed water on the basement floor around the forced air units last week during the heat wave. At time of arrival, water evaporation has occurred but the mineral deposits left behind are showing signs of water coming from most likely the air conditioning unit. Floor drain does not show any signs of back up and all other plumbing checks out fine including the water heater. Ran both lower and upper air conditioning units for approximate 10 minutes to find no leakage during that span of time. Replaced both owner furnished air filters at both units in the basement. Existing filters were not that dirty. Scheduled with Alex to have a heating air-conditioning technician out tomorrow Tuesday, June 29 8 AM First call. Enrolled in the Gold Maintenance Plan for one year.
Aaron w arrived on-site check in with customer Brandon went through ac forms found bad duct seal and filter all factory specs checked out no other problems found at visit offered bvr membership declined no warranty collect on-site paid in full credit card visa 354.00 need coil clean ducts sealed offer estimate need make decisions on departure unit working on normal functions.
One Platinum Plan, One Silver Plan and replace 30 Amp Contacter and 45 MFD capacitor. AC tune up in Morrison CO
Arrived at address to an ac that stopped working the night before. Per customer, the system may have frozen, she turned it off and replaced filter. Customer restarted ac this morning and has been working since. Checked levels of refrigerant and it was a little high on head pressure. Rinsed off the condenser and brought head pressure down. No issues at this time. Normal operation. Paid 240.00 via cc. Work complete. BVR member. Roke.
Furnace repair in Morrison
Drain Floor break centennial, co
Partial re-pipe denver co
Partial re-pipe denver,co
House drain line re-pipe Morrison co
Furnace tune up and service
Water leak above basement ceiling in Morrison.