Knowledgeable , helpful and pleasant.
The job was well done.
Chris McQuistion came out due to issues with boiler. Performed diagnostic. Found system to be piped in wrong. Found auto feed valve is faulty. Found pressure relief valve is compromised due to this. Found expansion tank has failed. Found auto air vent has been compromised. Gave customer options. Got permission to perform work. Went and grabbed components. Came back wi5 correct components. Shut boiler down. Drained entire boiler. Took out all faulty parts. Replaced auto air vent with brand new auto air vent. Replaced expansion tank with new expansion tank. Added shut off and tee for easier replacement in future and to tie in water line to boiler. Next replaced pressure relief valve with new relief valve. Next piped in new auto feed valve with new ball valves for isolation. Capped off other half inch line from original water line entry. Turned water back on tested for leaks. Found no leaks at this time. Purged all air out of system. Tested system. System is heating and operational at thi
Installed a 5/8 HP, evergrind, garbage disposal. Installed with a new drain tailpiece, and power cord. Total to be billed. Tech: Tomas.
Secondary and treatment Pulled apart drain and pulled full blockage. *refer to pictures. Ran the line with no issue and water tested with no drainage issues.
Chris Rosales out to tune furnace, customer signed up for gold membership and needs to clean condenser and fix leak on condensation drain line. Customer agreed to all repairs, once repairs where done customer paid $805.90 on a credit card. Unit is heating according to manufacturers specifications.
HVAC tech needed, and scheduled. Tech: Tomas.
Install three ways for the downstairs lighting. Install customer provided exhaust fan in the upstairs bathroom.
Minor repair on 3 handle shower valve. Tech: Tomas.
Membership, add two service stops under kitchen sink. Standard ot trip charge. 1 year parts and labor warranty. Paid $528.55 by card.
TJ tested sump pump and found it to be functioning properly. No charge. Warranty work. Original warranty.
Installed 1/3HP Zoeller sump pump, with 1&1/2â€ Zoeller check valve. Tech: Tomas.
Refer to Chris M notes
6/18/21 Dieudonne, I am here at the address above, Concern: customer requested ac tune up and check. See attached forms for tune up and check. Ac is working normally at this time. Total cost of the service today is $305 paid by credit card, customer had $50 coupon.
Drain clean mop sink wheat ridge Ran Spartan 100 out to clear obstruction in prep area floor sink. I ran lots of hot water to test and working properly now, however there is another string of floor sinks near prep table in front of house that is separate which is backing up they did not want to have these cleared. I recommended to have grease interceptor pumped out, and have us come back to give an estimate on getting all four sinks and drain lines in kitchen area. I also recommended to have changes in triple sink areas replaced as well as Cleaning out strainers and floor sinks. Also suggest replacing atmospheric vacuum breaker at mop sink area. Thank you
Started up evap cooler. Showed home owner how to operate water in case they need to use the water hose. Everything operating properly at this time
Boiler repair in wheat ridge