Knowledgeable , helpful and pleasant.
The job was well done.
Ran secondary line from floor she would do a load of clothes and it would back up i tested the toilet and shower numerous times to insure it wasnâ€™t a mainline the only response I got was when I ran water through the laundry line. Blockage cleared about 15 To 20 feet out for some reason it pulled back roots but mainline was running fine
Unit is 6 years old and it is in perfect working order. Two things found is that unit does not have expansion tank on unit also not pan under unit. At this time customer is ok with Original installation of water heater.
Home is 6 years old. No plumbing issues at all.
Furnace repair Wheat Ridge
Chris Rosales came out due to no heat, upon arrival found unit on, recommended tune up to find cause of problem, customer agreed to membership tune up. During tune up discovered pressure switch would not stayed closed error 46. Customers furnace installed 2017, unit is under warranty, will pick up parts and install tomorrow. Customers flue vent has no slope and needs to be redone tomorrow. Dispatch to schedule job for tomorrow morning. Chris Rosales came back the next morning and redid flue vent for efficiency and to have slope so combustion motor and pressure switch does not fail again. Warranty on flue and pressure switch 2 years. Unit is heating at this time. Customer paid $139.00 on check.
Installed 40 Gallon 40,000 BTU Bradford White Water Heater. Paid in full with a card. Tech: Tomas.
Below is a summary of your pipe repair.
Looked at leaky Delta kitchen sink faucet. Looked at outside hydrant on back of house that was leaking. Customer was shocked at price
Drain cleaning Wheat ridge
Chris McQuistion came out due to issues with boiler. Performed diagnostic. Found system to be piped in wrong. Found auto feed valve is faulty. Found pressure relief valve is compromised due to this. Found expansion tank has failed. Found auto air vent has been compromised. Gave customer options. Got permission to perform work. Went and grabbed components. Came back wi5 correct components. Shut boiler down. Drained entire boiler. Took out all faulty parts. Replaced auto air vent with brand new auto air vent. Replaced expansion tank with new expansion tank. Added shut off and tee for easier replacement in future and to tie in water line to boiler. Next replaced pressure relief valve with new relief valve. Next piped in new auto feed valve with new ball valves for isolation. Capped off other half inch line from original water line entry. Turned water back on tested for leaks. Found no leaks at this time. Purged all air out of system. Tested system. System is heating and operational at thi
Installed a 5/8 HP, evergrind, garbage disposal. Installed with a new drain tailpiece, and power cord. Total to be billed. Tech: Tomas.
Secondary and treatment Pulled apart drain and pulled full blockage. *refer to pictures. Ran the line with no issue and water tested with no drainage issues.
Chris Rosales out to tune furnace, customer signed up for gold membership and needs to clean condenser and fix leak on condensation drain line. Customer agreed to all repairs, once repairs where done customer paid $805.90 on a credit card. Unit is heating according to manufacturers specifications.