Today we performed a Bensons level winter tune up on your two Goodman heat pump units, everything is working properly at this time. Thank you for your business. Apalachicola Fl
I dropped off a box of air filters in Tallahassee
I performed a winter time tune up on a Goodman heat pump in Apalachicola
Performed a gold level tune up on the equipment. Testing system operations, component amperages, capacitor ratings, and cleared the drain line. Found the dual run capacitor dead, a faulty condenser fan motor with seizing bearings, and a pitted up contactor. We replaced the dual run capacitor and contactor and ordered a factory condenser fan motor. We will have to come back out to install the fan motor once it arrives. The system is cooling at this time but the fan could go out at any time. Apalachicola Fl
I installed a new blower motor as agreed. I also installed a new 15uf capacitor and a new blower relay. The system is operating properly at this time.
Dropped of a case of filters.
The customer signed on the Gold esa plan.
Preformed Pre-paid Gold Level ESA maintenance 1st visit on one heat pump system in cool mode. The 14x24x1 filters needs to be changed and cleared the drain line. The customer was emailed a copy of the maintenance report. I found that the indoor blower motor is amping high and it is leaking out a lot of grease. The leaking grease is signs that the bearing are going bad. Overall the system is cooling properly at this time. I recommend installing two Surge Protectors one for the air handler and one for the condenser, to protect against power surges and brown outs. I quoted the customer for a new blower motor and surge protectors.