Air handler #3 (Office) Found a restriction in the suction line at condenser. I replaced the evaporator coil and thermal expansion valve in the air handler. Pressure tested system with 350 pounds of nitrogen to check for leaks, pulled system down on a deep vacuum, recharged with a factory charge of 15 pounds of refrigerant, and fired the system off. The system is now cooling properly at this time. This repair is covered under their 2 year labor, 10 year parts warranty.
Replaced the faulty control board in the air handler of the living room air conditioner under warranty. The system is now working properly at this time.
Performed a summertime tune up on the Hvac equipment. Testing system operations, component amperage’s, cleared the drain lines, checked the air filters, cleaned the air handlers, and cleaned the condenser coils outside. The air conditioners, dehumidifiers, and wine cooler are all working properly at this time. Billable
Replaced faulty module and interface controller on system #2 under warranty. Interface controller SYSTXCCIC01-B/ 1921W200581 Air handler FE4ANB006/ 0721F06664 Condenser25VNA460A00310/ 1421E19746
Performed a summer time tune up on the Hvac equipment. Testing system operations, thermostat functions, cleared all the drain lines, cleaned the condensers outside, and replaced all the Carrier High Media Filters. The systems are working properly at this time in air conditioning mode. I turned off the filter reminder notice on each of the thermostats per homeowners request. Billable
I performed a Gold level Summer time tune on your equipment today. Checking the systemâ€™s operation. Thank you for your business today. Tallahassee, Fl