Nick was on time, answered all my questions and let me watch him do the job, very satisfied!
I was unable to be at the house for the maintenance visit, but Phillip called on his way there and called again before he left the house, which I really appreciated. He was timely and professional.
Jayshawn was polite and helpful. He explained what he was doing and answered all my questions.
He did a great job and was very professional
Phillip was very polite and efficient! Helpful too! He told me I had "gold" status which no one has told me before! Apparently I'm entitled to free filters which he said he would send me!
The serviceman was very helpful in explaining things to me. Thank you
Robbie Robins is an excellent technician and does a great job.
Robbie is a great technician and does an excellent job!
Curt arrived on time and performed the service efficiently and effectively. Curt was very courteous and professional.
I was able to locate the correct Heat strips for the York rooftop unit they are 14kw 480v and we should have the first of the week. I returned today to complete the repair work on the York rooftop straight cool system. I installed the new 14kw Heat Strips and verified that they were working after installation. Thank you for your business today. Bainbridge,Georgia.
Today I preformed a winter time maintenance on your Heil heat pump and Gree mini split system. I discovered that your primary drain line safety switch is faulty and should be replaced. Other than that, both of your systems are working properly at this time.
I performed a winter time maintenance on your HVAC equipment. Here is a summary of the work completed: Overall Equipment Condition: Good Location, Type, and Picture of Indoor Unit: Closet, Air Handler Area Unit Services: The air handler is in the bedroom closet and services the whole house. Filtration: Pleated 1", Replaced Today Filter Size: 16x20x1 Condition of Indoor Coil: Good, Clean Location, Type, and Picture of Outdoor Unit: Side of House, Heat Pump Condition of Outdoor Coil: Good, Clean, Cleaned Today I tested and inspected the following electrical components on your equipment, and they are working properly within the manufacturers recommended specs and amperages: Blower Motor Heat Strip Kit Condenser Fan Motor Compressor Blower Run Capacitor Compressor Run Capacitor Fan Run Capacitor Contactor Electrical Wiring There were no electrical components found to be not working properly or not within the manufacturers recommended specs and amperages. I inspected the following compone
Today I performed your wintertime tuneup, verifying the systems operation and to make sure everything was functioning properly and heating mode. I cleaned and inspected the unit including items, compressor, outdoor fan, motor, indoor fan motor, capacitors and check the wiring and defrost control board along with all the capacitors. The system is operating properly at this time thank you for your business Bainbridge, Georgia View visual findings from this job here - https://visionshare.xoi.io/?id=XA-6E7D-E6DB2C6C4FEE42058020F4A742D5DC5E
Today I performed a wintertime tuneup on your York heat pump unit. Everything is working properly at this time. Thank you for your business. Bainbridge GA
Recovered refrigerant from the system, removed old TXV and filter drier, installed new TXV and filter drier, pressure tested the system with 330 pounds of nitrogen and found no leaks. Pulled a deep vacuum under 500 microns and weighed the recovered charge back into the system. Found the high side pressure topping out at 430 PSI on a long heating run, a drastic improvement from the 620 PSI caused by the bad TXV. The system is heating and cooling properly at this time. Thank you for your business. Bainbridge GA
Today I performed a wintertime tune up on your American Standard heat pump unit. Everything is working properly at this time. Thank you for your business. Bainbridge GA View visual findings from this job here - https://visionshare.xoi.io/?id=XA-20A5-6DEF41F3DE434A9CBD1B030D6AD25D4A
Today I performed a summer time tune up on your Amana and Lennox heat pump units. Everything is working properly at this time. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-FF01-5A0146BD8F3C41AFBAC637041D357AEA
Customer called in requesting service at the Bainbridge Goodwill. They were concerned about the system not cooling properly. Upfront and in the back loading area. No after arriving today I spoke with employee about their concerns. She informed me that the system was having intermittent issues somedays it would cool better than others. They would like for us to check over both units to make sure they were running properly. I began with the York unit and checked the Blower motor, outdoor fan, compressor as well as the electrical components that system is in working order. I did not find any areas of concern. I then moved to the Daikin system and checked the compressors outdoor fans and blower motor. I checked the evaporator coil and condenser coil and found the source for the concerns. The coils both evaporator coil and condenser coils need to be cleaned. The dirty coils are the reason why the system is not cooling as it should. The restricted air flow will not allow the system to keep t
Managers house- found the compressor not coming on due to a faulty dual run capacitor in the package unit. I replaced the capacitor with a new one and the system came on. I tested system operation, component amperage’s, and thermostat functions. The system is now working properly at this time. Billable. Sent proposal to add this location to the maintenance agreement for River Ridge.
Today I performed a summer time tune up on your Bensons and ruud Heat-pumps, your systems are working properly at this time.Tallahassee Fl View visual findings from this job here - https://visionshare.xoi.io/?id=XA-4BD6-26122DD953764E51A138F59E9B43EE6B
Today I performed your annual summertime maintenance. I checked all of the systems wiring the capacitor on the blower motor as well as the dual run capacitor check the amperage on the blower motor amperage on the compressor and outdoor fan motor. The system is operating properly in cooling mode. Thank you for your business today. Bainbridge Georgia. .
Today I performed a summer time tune up on your American standard heat pump unit. Everything is working properly at this time. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-0090-2F94BCCC46B249DBBD35B87F8BA7ECE3
I performed a summer time tune up on a Amana and Lennox Air Conditioner unit Thank you for your business View visual findings from this job here - https://visionshare.xoi.io/?id=XA-92BE-0418D2566E544045A99380AF3B87DFE6
Capacitor replaced under warranty system working properly at this time. Paid via card on file. Thank you for your business.