The serviceman was very helpful in explaining things to me. Thank you
Robbie Robins is an excellent technician and does a great job.
Robbie is a great technician and does an excellent job!
Curt arrived on time and performed the service efficiently and effectively. Curt was very courteous and professional.
Performed a Gold level summer time tune up on your American Standard equipment today in Bainbridge, Georgia . Thank you for your business today.
Performed a summer time tune up on an American Standard system in Bainbridge, Ga.
Found the condenser shutoff on a High pressure lockout. The suction (low) side psi was 275 when recommended psi for the low side was 235. Removed roughly a pound of refrigerant to bring pressure down a bit. The system is working properly at this time.
Performed a winter tune up on a Goodman heat pump in Bainbridge. Tested system operations and component amperages, changed 1 20x20x1 pleated filter. The system is working properly at this time.
I preformed a winter time tuneup on a Rheem and an ICP heat pump in Bainbridge, GA. Checked system operations, component amperages, tested capacitor ratings, cleared the drain lines, checked the filters, checked batteries in the thermostat, cleaned return grills, and cleaned the condenser coils outside. Systems are both working properly at this time. Both air handlers in the attic have no primary or secondary safety switches, sent estimate to install primary drain switch for both air handlers to help prevent water overflow in the event of a clogged drain line.
I performed a Gold level winter time tune up on the equipment. Testing syst operations, component amperages, capacitor ratings, cleared the drain line, replaced the air filters, dusted the return grills, checked the thermostat, and cleaned the condenser outside. The system is working properly at this time in heating mode. Thank you for your business today. Bainbridge,Ga.
A maintenance could not be performed on the York system as it is not operational, we recommend replacing it due to the phaseout of R22 and high cost of repair. We will reach out to provide an estimate on a new system. A full maintenance was completed on the Daikan system and it is working properly at this time. Thank you for your business. Tallahassee FL
Diag water dripping from unit. Found clogged drain line causing primary safety switch to shut off system. Cleared drain line with nitrogen and flushed with several gallons of water. Poured water into primary drain pan to ensure water was draining properly. Dried return cabinet below unit and reconnected drain line. Tested system and it has a good split (53/73). System is working properly at this time. No charge as maintenance was preformed last month.
Today I performed a winter time tune up on your American Standard heat pump unit. Everything is working properly at this time. Thank you for your business. Bainbridge, Georgia
Customer needs to reschedule appointment, waited the 30min left door tag.
Performed a summer time tune up on a Goodman system in Bainbridge.
Today we performed a tune up on your American Standard package unit and American Standard heat pump unit. The upstairs unit is not working properly at this time. We will send a service tech to diagnose the issue. Thank you for your business. Tallahassee FL
I performed a summer time tuneup on your Amana heat pump and Lennox heat in Bainbridge. Thank you for your business!
Preformed Pre-Paid Gold Level maintenance 2nd visit on 2 heat pump systems in heat mode. The 20x25x1 and the 20x30x1 filter was good and the drain line was cleared. The customer was emailed a copy of the maintenance report.
I performed a winter time tuneup on a Lennox heat pump and on a Goodman heat pump in Bainbridge, GA.