Performed a summer tune up on a Lennox heat pump in Metcalf Georgia. Tested system operations and component amperages, cleared drain line with shop vac and 2 gallons of water. Checked filters, let customer know that the system is 17 years old and the condenser coil is dry rotting. Sent customers contact info to Rob K for quote to replace system. The system is working properly at this time.
Today we performed a Gold level winter tune up on your Lennox heat pump unit. We installed a surge protector on the outdoor unit to protect the unit from any surge or blow out. We did not get a good temperature split between the return and supply in cool mode but we did get a good one in heat mode. Everything is working properly at this time. Thank you for your business. Metcalf Ga