I performed a geothermal clean and tune. Also changed the filters. The unit is generating 46560 Btus which is what the manual specifies. I put some insulation on a couple pipes that were condenasating to help stop and water drips. The unit is operating properly.
Performed geo clean and tune. Cycled the system. Tested the heat of extraction. 10.5x500x5=26250 btu. The heat of rejection is good. The geo unit is operating properly.
Installation looks great. Owners are happy. Randyâ€™s Electrian is upgrading the panel and will wire the unit once that is done.
Completed install of new mini split ac, heat pump system. Installed 1- 9,000 btu unit in master bedroom, and 1- 12,000 btu unit in living room. Ran linesets to exterior of the home to outdoor condensor. Ran drain line for master bedroom unit to exterior and drain line for living room unit to sump pit in the basement. Covered exterior master bedroom line set with line hide. Pressurized lineset to 300 psi with nitrogen to check for leaks and then used vacuum pump to evacuate to 345 microns. Run tested all equipment. Customer will need to get a 220 volt federal pacific circuit breaker to provide proper power and circuit overload protection to outdoor condensor. The existing breaker we connected to does not provide the proper voltage and therefore cannot be used. Please provide us with a phone call and an email with a picture showing the new proper breaker. Thank you for choosing Black-Haak, please take a moment to fill out our online survey.
Provided power for mini split installation, power was provided to 60amp non fused disconnect and GFI in disconnect. Power was distributed out of disconnect to the unit.