First year furnace clean and tune. Cycled system. Checked heat exchanger, ok. Checked and cleaned flame sensor and burners. Checked gas pressures and adjusted to maximize efficiency. Checked for CO in airstream, none found. Normal levels of CO and XS air in exhaust, normal levels found. System operating normal at this time. Job complete.