No cool. The condenser wouldnâ€™t turn on with a cooling call. I checked the electrical compartment and found a wire burnt off the contactor. I reconnected the wire. The contactor, capacitor and compressor are worn and in poor shape and causing the unit to burn up wiring. The air conditioner is cooling now. The air conditioner is 15 to 20 years old. I recommend replacing the air conditioner because the compressor is drawing more amps which is causing the wires to burn up, it will most likely do this again.