We have a geo system installed by Black-Haak and it has worked well over the last couple years. We have saved money and hassle by not dealing with oil or propane anymore. Thank you all.
Performed geo clean and tune. Tested the performance of the unit. Itâ€™s producing 28,000 btu of heat which is good. The geo unit is operating properly at this time.
Boiler leak. Upon inspection there is a leak on the top of the expansion tank. Removed old tank and installed new tank. Filled and purged unit. Ran and tested unit. All systems operating at this time. Recommend customer to get cleaning done on boiler.
Performed first year furnace cleaning; started by inspecting the exhaust and intake PVC ensuring all connections were secured, I then removed and cleaned burners along with the flame sensor, next i sniffed out the gas line verifying no leaks, I then cycled the system on and checked gas pressures and did end up making an adjustment on first stage, lastly I ran a combustion test verifying no CO in the airstream as well as re did the drain line for better pitch. This system is currently operating normal at this time. Job complete
Completed new installation of a Tempstar 2 ton AC system. Installed the evaporator coil in the plenum above furnace and set the condenser on a pad on the exterior of the home. Ran refrigerant lineset between the new condenser and coil and brazed it to each. Ran a new drain line from the coil and tied it into existing furnace drain. Pressurized the lineset with 325 psi nitrogen to test for leaks and then evacuated to 400 microns. Released the charge but due to the temperature was unable to do a start up procedure. Will return in the spring when above 60 degrees to check refrigerant charge. Thank you for choosing Black-Haak heating. Please take a moment to fill out our online survey.
Replaced transition assembly. Performed furnace clean and tune; removed and cleaned burners along with the flame sensor did find a couple spots chipped in the flame sensor, I ohmed out the igniter and that tested week, I then did a powder test on the heat exchanger and did get blow back from left cell I removed coil patch to get a better look at the heat exchanger and did find a large amount of rust on that left side but no crack, I then cycled the system on and ran a combustion test verifying no CO in the airstream, lastly I came across a section of exhaust that was not glued I glued this section to prevent any issues. I recommend replacement on both the igniter and flame sensor. This sytem is currently operating normal at this time job complete
Was here for a package cleaning. Will be returning for the air conditioner in the spring. Performed preferred customer furnace cleaning. Completed furnace cleaning form. Furnace is running normally at this time. Office to mail the invoice.
Installation of hepa filter complete
Found unit operating on arrival. Checked pressure at pressure switch. Pulling 2.4 inches. Blew out drain trap. Checked propane level. Furnace is working at this time. Drain trap was restrictive enough to restrict water flow but let it drain over time.
Installed a new furnace.
Performed a cleaning and tune-up on the geothermal system.