No heat. System was firing when I arrived. I checked filter and found it ok. Checked drain lines. Found clogged line. Cleared drain line. Found standing water in burner compartment. This may be due to the blockage in the line. Cycled system. System fired as normal. Found some water in the lines from pressure switches. Recommend bringing pressure switches to the cleaning and replace under warranty. Job complete. System operating normal at this time.