Parts are on order and furnace is working for now, parts to come next week. Dan explained things in terms I could understand and am following his recommendation to the letter. May be pricey, but get only what you pay for today.
We were happy with the service provided and the explanation of our problem with our AC and then having the manager come out to also take a look to see if he agreed with the issue. Nice to know they have our back.
would recommend you to anyone
Kody Wojtalewicz was very Professional, I felt he went above and beyond, A plus service.
Replaced bad outlet in bedroom
Performed start up on the heat side of the packaged unit. Checked over the wiring. Cycled the unit. Set the gas pressure and performed a combustion test. The package unit is running normally at this time.
Filter was delivered and installed.
Performed generator maintenance and inspected battery. Battery voltage was good, replaced air filter, replace oil and oil filter, replaced spark plugs.
Ac clean and tune. Checked drain line. Checked condenser. Checked compressor, found lower on ohms. Fan motor and compressor tested in caution. Capacitor and contactor are both very worn and weak. Used coil cleaner on condenser coil. Hooked up gauges and checked pressures and temps. Subcooling was at 13. Indoor temp split was 18. Average life of this unit is 14. This unit is well over that and very worn. Future failure is expected. System operating normal at this time. Job complete.
installed 2 receptacles with bubble covers near the area that the lighthouse will be placed. One receptacle is controlled via photo eye. Replaced receptacle near pump and installed bubble cover.
Performed the new furnace start up. No gas leaks detected. Gas and exhaust levels are normal. No CO detected in the air. Venting and electrical components are properly installed. Heat rise was 38 degrees. High limit passed safety check. Unit is heating properly at this time.
Installed new Daikin DM96VE080 gas furnace. Also installed T6 WiFi thermostat. Offered electrostatic filter upgrade and humidifier replacement. May upgrade and/or replace at time of A/C replacement. A/C coil pan is leaking and needs to be replaced.
Was here for a furnace no heat. The furnace wasnâ€™t running when I got here. Reset power to the furnace. Cycled the furnace. The burners would light but the blower motor wouldnâ€™t turn on. Found that the circuit board wasnâ€™t allowing power to the blower motor. The furnace is 17 years old. Recommended that they get a second opinnion with my supervisor Dan to go over repair or replace options. Office to schedule Dan for 9am on Monday morning.
Performed first year furnace cleaning; inspected the exhaust and intake PVC ensuring all connections were secured, removed and cleaned the burners along with the flame sensor, cycled the system on and performed a combustion test verifying no CO in the airstream, also did a refrigerant leak search on the Acoil and did find indicators of a possible leak on the AC system. This system is currently operating normal and heating at 53 degrees at this time. Second opinion scheduled with Dan F today at noon Job complete
Boiler would make a whiny noise. I cycled the boiler. When it had an output of 150000 btu the exhaust blower shroud would vibrate and make a noise. I removed the shroud. We will need to order a new exhaust blower and come back to install it. The boiler is heating at this time.
No heat on oil furnace. The burner was locked out. I checked the cad cell, it was good. Checked clean outs, they were clear. Cycled burner. The burner would try firing but it wasnâ€™t getting constant oil flow. I bled air from the oil line. Cycled the furnace multiple times. Itâ€™s heating properly now. No charge since I just cleaned it and forgot to bleed air out of oil line.
No heat on geo unit. I checked unit for fault codes. Found a flow switch fault code. I cleared the code and cycled the geo. It cycled through hydronic heat normally. I checked the flow switch, found it wasnâ€™t aligned correctly on the pipe. I corrected the flow switch alignment. Checked flow center water level. Water is to the top. Level is good. Cycled geo in forced air heat. Itâ€™s working properly.
We removed the old furnace and installed a new tempstar furnace. We reconnected all duct, gas line, venting and electrical. Ran new drain line for the furnace only. Cycled the unit, everything is running fine. Thank you
No heat. Cycled system furnace fan and ventor motor both run. Giving code of 4. Checked and cleared condensate trap. It was plugged. Also, found pressure switch was not making. Cleared all pressure lines and removed intake venting. Pressure switch would work if pressure was put on the top of it. Recommend replace pressure switch. Adjusted hose and pressure switch held. Office to quote pressure switch replacement and schedule furnace clean and tune. Furnace is heating at this time. Office to schedule ac clean in spring. Job complete.