I truly liked the "I'm on my Way" text message showing a pic of the service tech and the short bio...I've not seen this before but I enjoyed the information. Tech was on-time, efficient and provided a full update and invoice before leaving, can't really get much better than that...
I recently purchased a home with boiler heat. Noticed a small leak from one of the water lines. It was only a small leak and decided to call Black-Haak heating because there was a sticker on the boiler. I wasn't sure if they did the pipe repair or if I should hire a plumber. Black Haak had Brad over at the house later that day. Very professional. Explained what the process would be. Had the repair scheduled for a later date. Brad had the whole system drained, pipe and valve changed out and had my system operating within a couple of hours for far less than I was expecting. If you need service on a hot water boiler heating system....Brad at Black-haak Heating should be your first and only call.
Installed new gas furnace and AC. Furnace is up and running and tested. AC has not been pumped down yet under pressure to cold.
Installed indoor air quality package with a 16x20x1 electronic air cleaner, a Aprilaire humidifier 600, and a PureAirX ultraviolet light. We cycled the system on to ensure operations. This system is currently operating normal at this time job complete
Performed boiler clean and tune. The sparker gap was starting to widen. I replaced the sparker. Also secured the drain trap to the boiler. The boiler is operating safely at this time.
Located short in receptacle in 3-seasons room also did voltage check on circuit in panel.
Performed furnace start up; inspected the exhaust and intake PVC ensuring all connections were secured weâ€™ll have to return next year with spray foam to insulate the exhaust and intake PVC, sniffed the gas line for possible leaks, as well as cycled the system on and checked gas pressures and did make adjustments on both stages, also performed a combustion test verifying no CO in the airstream. This system is currently operating normal and heating at 47 degrees at this time. I did include a quote for an electronic air cleaner because i notice the du point allergen filter the air cleaner uses a positive electronic charge to help attract those fine particles down to .3 microns in size eliminating those particles that can upset allergies as well as included a quote for a humidifier replacement because the one in place now has a broken solenoid valve. Job complete
2/14/19. Removed old furnace. Installed new daikin 2 stage. Cut holes in wall to outside and ran pvc for exhaust and intake on furnace. Installed metal to connect furnace to duct. Reconnected electrical and thermostat wiring to furnace. Connected gas piping to furnace. Ran new drain hose from furnace and coil to floor drain. Installed t6 WiFi stat and set it up. Thank you for choosing Black-Haak heating for your heating needs.
System was abruptly shut off due to a power outage. Upon arrival I found the Tstat set to 55 degrees I changed the set point to 75 and cycled the furnace on. The system functioned properly without any issues I checked the kitchen stove and found the clock displaying incorrect time as well as flashing. System operating normal at this time. Would recommend,Ed getting a Tstat with batteries to prevent the furnace from shutting off. Job complete
Performed level 2 furnace cleaning and replaced the inducer motor. I had to completely disassemble the furnace venting and gas pipe to get the motor out. After installing the new motor and put everything back together, I was able to perform the cleaning. Burners are clean. Heat exchanger and ignition assembly are showing signs of wear. Gas and exhaust levels are normal. No CO detected in the air. Heat rise was 50 degrees. Due to age and condition, annual maintenance is recommended. Furnace is operating normally at this time.
Performed furnace start up; inspected the exhaust and intake PVC ensuring all connections were secured, sniffed the gas line for possible leaks, cycled the system on and checked gas pressures and did make an adjustment, as well as performed a combustion test verifying no CO in the airstream. This system is currently operating normal and heating at 54 degrees at his time. Job complete
Installed Honeywell T4 thermostat. As well as installed 16x25x1 electronic air cleaner. Job complete
1/17/19 removed old furnace. Installed new Goodman furnace. Installed new 3â€ pvc venting. Reconnected electrical and thermostat wiring to new furnace. Ran new drain hose from furnace and coil to floor drain. Installed metal to connect furnace to duct. Started furnace and everything is running and draining properly. Thank you for choosing Black-Haak heating for your heating needs.
Performed first year furnace cleaning; inspected the exhaust and intake PVC ensuring all connections were secured, removed and cleaned the burners along with the flame sensor, cycled system on and checked gas pressures and did make an adjustment, as well as performed a combustion test verifying no CO in the airstream, also replaced the 16x25x1 air filter, lastly made a fan adjustment to get a temp rise of 50 degrees. Also want to make note of the air quality report we had higher levels of particles in the home which could result in build up on the blower wheel which could cause great reduction in efficiency I would recommend upgrading the filter to an electronic air cleaner to bring these levels down. Job complete
No heat when thermostat set to auto. Inspected thermostat and furnace. Checked voltage for fan set to auto mode and there was none. When the fan is set to on the low speed fan kicks in and runs while burner is on. All other systems are operating safely at this time.
Exchange 100 amp panel and sub panel to a new 32 space main breaker.