I truly liked the "I'm on my Way" text message showing a pic of the service tech and the short bio...I've not seen this before but I enjoyed the information. Tech was on-time, efficient and provided a full update and invoice before leaving, can't really get much better than that...
I recently purchased a home with boiler heat. Noticed a small leak from one of the water lines. It was only a small leak and decided to call Black-Haak heating because there was a sticker on the boiler. I wasn't sure if they did the pipe repair or if I should hire a plumber. Black Haak had Brad over at the house later that day. Very professional. Explained what the process would be. Had the repair scheduled for a later date. Brad had the whole system drained, pipe and valve changed out and had my system operating within a couple of hours for far less than I was expecting. If you need service on a hot water boiler heating system....Brad at Black-haak Heating should be your first and only call.
1/17/19 removed old furnace. Installed new Goodman furnace. Installed new 3â€ pvc venting. Reconnected electrical and thermostat wiring to new furnace. Ran new drain hose from furnace and coil to floor drain. Installed metal to connect furnace to duct. Started furnace and everything is running and draining properly. Thank you for choosing Black-Haak heating for your heating needs.
Performed first year furnace cleaning; inspected the exhaust and intake PVC ensuring all connections were secured, removed and cleaned the burners along with the flame sensor, cycled system on and checked gas pressures and did make an adjustment, as well as performed a combustion test verifying no CO in the airstream, also replaced the 16x25x1 air filter, lastly made a fan adjustment to get a temp rise of 50 degrees. Also want to make note of the air quality report we had higher levels of particles in the home which could result in build up on the blower wheel which could cause great reduction in efficiency I would recommend upgrading the filter to an electronic air cleaner to bring these levels down. Job complete
No heat when thermostat set to auto. Inspected thermostat and furnace. Checked voltage for fan set to auto mode and there was none. When the fan is set to on the low speed fan kicks in and runs while burner is on. All other systems are operating safely at this time.
Exchange 100 amp panel and sub panel to a new 32 space main breaker.
Black Haak would be pleased to move the (3) existing wiring into the wall where needed. We will also move the (2) gang switch box to the location you will need them at once the pantry is framed. The items are all in the photo attached. We will also install a pantry light on a door switch.
Quoted an electrical upgrade.
Replaced water pressure switch. I cycled the unit a few times as well to make sure I had no fault codes. Unit is operating normally at this time.
Came out to replace a main board. Board was bad, however, unit still wouldnâ€™t ignite. We have a bad pressure switch. There is proper voltage but not the right amount of water column. I tried to do other test as well to make sure that was the issue. Gas valve had 24v and hot surface igniter was lighting. Pressure switch wouldnâ€™t allow flame to ignite due to the water column. Myself and Jerimiah were able to temporarily get the unit to heat, however, it will fail again. We need to return with parts ASAP.
Performed level 2 furnace cleaning. Unit was very dirty with rust chips when I arrived. Burners and pilot assembly are wearing out. Heat exchanger is very worn and has a lot of chipping. Inducer motor and gas valve bearings are starting to sound worn as well. Average life of system is typically 12-14 years. Unit is currently around the 20 year mark. Due to age, condition, cost to repair, and safety concerns in the future, second opinion is recommended.
11-14-18 installed humidifer and uv light. Tested so both are opperating.
Performed start up on new furnace. No gas leaks detected. Combustion analysis was normal. No CO detected in the air. Electrical and venting components are properly installed. High limit passed safety test. Heat rise was 46 degrees. I asked customer about adhusting the flame and he didnâ€™t think the home was heating up quick enough. I found the filter was dirty and clogged. This may have been the issue. Gas pressures were normal. Unit is operating great at this time.
Completed 80% gas furnace replacement. Disconnected and removed old furnace. Set new furnace on blocks and reattached the ductwork, gas, electric and AC coil drain. Ran a new vent pipe into chimney. Run tested the furnace but will still need a technician start up. Thank you for choosing Black-Haak heating. Please take a moment to fill out our online survey.
Installed (2) floor receptacles and hung new dining room light
Water was leaking from the furnace. Found the collector box in the furnace is cracked causing the water leak. Also Jayne said the hrv timer wasnâ€™t working. I took a look at the hrv. Itâ€™s running but the timer is broken and not working properly. We will get approval to replace these parts and come back to replace them.