Hunter was very knowledgeable and was a very nice and friendly
Excellent service and comuunication
He arrived on time and was fast. He explained everything he did very well
I truly liked the "I'm on my Way" text message showing a pic of the service tech and the short bio...I've not seen this before but I enjoyed the information. Tech was on-time, efficient and provided a full update and invoice before leaving, can't really get much better than that...
The new air conditioner wasnâ€™t keeping up during the day. I cycled the air conditioner and checked the charge. Found the condenser coil was plugged with cottonwood. I washed the condenser coil. Checked the charge. It was low on charge. I added a pound of refrigerant to get the proper charge. I checked the split, it was at 19. Checked the air handler. Found the sensing bulb wasnâ€™t insulated. I insulted it. The air conditioner is cooling properly at this time. We need to come back to adjusted the lineset in the attic. Office will call to schedule that.
Customer stated that he had a no cool yesterday. TXV and service valves were frozen. Hooked up gauges and checked pressures and temps. Found coil temp low at 23 degrees. Filter is ok and no obstruction on evaporator coil. Added 1 pound 4 oz of R410-A refrigerant. High side went up, but suction side remained under freezing. Checked indoor coil and found half of the coil was freezing up and the upper half was warm. This indicates that there is a problem with the TXV not opening. Office will follow up with pricing for new TXV. warranty will be checked. Maintenance will be done after cooling issue is resolved. No payment collected at this time. System not cooling correctly at this time. Job complete.
Performed AC clean and tune, replaced 20x25x1 filter, inspected condenser electrical compartment and tested components capacitor and contactor both showing signs of age, sprayed condenser with coil cleaner, cycled the system on and checked pressures and temps system is slightly overcharged cooling at 24 degrees. This system is currently operating but due to age and condition future failure is expected. I am including a quote for repair as well as a quote for a package cleaning so we can ensure safe furnace operations this fall. Job complete
No cool on the geo system. Found the geo was tripped on a water flow error. I reset the unit. The geo turned on. I checked the pumps, they were running. Checked the pressure drop and temperature rise across the heat exchanger. Had 13 psi drop and a eight degree temp rise. This is ok. Checked a temperature split of the ductwork. Itâ€™s at 25 which is good. I tested the freeze protection thermistor and found itâ€™s not reading correctly and caused the unit to not run. We will order a new thermistor. The unit is cooling at this time Also found the zone board isnâ€™t allowing the geo to operate in 2nd stage. I jumpered out the board so it will run in second stage. We will quote a price to replace the zone board as well. Office will call with price for the zone board and the thermistor. .
Performed air conditioner start up. Used vacuum pump. Released the charge. Cycled the air conditioner and set the fan speed. Added 2 pounds of refrigerant to the unit. The air conditioner is running normally at this time.
Performed air conditioner clean and tune. Washed air conditioner, checked electrical components. Found the capacitor getting weak. Cycled the unit and checked the Freon charge. The unit is a little low on freon and starting to frost up. I performed a electronic leak search. Found the evaporator coil and the condenser coil is leaking Freon. The air conditioner is going to fail. Air conditioner is 22 years old. Eric has a home warranty, he will call to get a claim number and we will get replacement authorization on Monday. Office will be in contact with you.
Performed the level 2 AC cleaning. No leaks detected. Electrical components are starting to wear. Condenser coil has bent fins. Refrigerant charge tested good. Subcool was 15Â° with a 16Â° temp split. Unit is currently cooling properly at this time. However, due to age and condition, we cannot gaurante a long life expectancy.
Removed old boiler, water heater, and controls. Installed new IBC boiler indirect and controls. Filled and purged system, flushed with f5 cleaners and then added fluid filter. Preformed start up and everything is operating properly this time Will see a bill for the indirect and boiler upgrade. We will mail the focus on energy paperwork. Thanks Brad
Performed the level 2 AC cleaning. No leaks detected. Electrical components tested good. Capacitor tested in the required zone. Condenser was cleaned with water and nu brite. Refrigerant charge was normal. Subcool was 12Â° with a 17Â° temp split. Unit is cooling properly.
Boiler has been needing to get reset every day. I checked the boiler. The ignition module was on a 5 minute retry cycled. The pilot lit, the gas valve would get power but it wouldnâ€™t open. I reset the boiler and gas valve, cycled the boiler the burners lit now. The gas valve is getting stuck close after itâ€™s off for a while we will return with the gas valve and replace it.
Pulled a 3â€ liner down the chimney and conneced to the water heater.
Performed preferred client furnace start up. Checked over the furnace installation. Cycled the furnace. Set the gas pressure. Took a temperature reading and set the fan speed. Performed furnace combustion test. The furnace is running normally at this time. Talked to the client about possibly getting the air conditioner checked out. The client will talk it over with his wife and call if they are interested.
installed new gas furnace and AC, all equipment tested and running start up complete on both units.
3-26-19. Removed old furnace. Installed new daikin 2 stage furnace. Installed metal to connect furnace to duct. Connected pvc to exhaust on furnace. Installed and setup t6 WiFi stat. Pulled new 6wire thermostat wire from upstairs to furnace. Reconnected gas piping and electrical wiring to furnace. Installed filter upgrade kit and new 213 filter. Ran new drain hose from coil and furnace to floor drain. Started furnace and everything running and draining properly. Thank you for choosing Black -Haak heating for your heating needs.
Installed new gas furnace and AC. Furnace is up and running and tested. AC has not been pumped down yet under pressure to cold.