I was here to replace the ignitor in the pool heater. I removed the failed ignitor and installed the new ignitor. Cycled the pool heater multiple times. The pool heater is operating properly at this time.
Replace leaking pvc fittings. Flushed out hydronic system with the hydrofill and took a water sample to compare to pre cleaning sample. Added protector into system. Rechecked loop field numbers: .975 antifreeze level and 14 gpm. All systems operating properly at this time. Thanks Brad
replace pool heat exchanger and purge out the lines start up and test all joints we worked on and everthing is operating properly Talked to the customer about getting a cleaning done on the geothermal. Performed cleaning on the geo and tested all components and electrical. Compressor and capacitor are good but the contactor is pitted and burned and we have to check warrenty. Geothermal unit is operating properly at this time. The filter is pretty dirty I didnâ€™t have one with me so we should check with Jeff and see if he wants us to put it in or drop it off. Thanks Brad
- presented proposal
I performed the geo clean and tune. I changed the filter, cleaned the drain. I checked the water level in the flow center, it was good. I checked and tested the electrical components, they are all working properly. Wiped out the unit. Cycled the geo unit and tested the performance. Unit is producing 42,000 btu of cooling which is good. Geo unit is operating properly.
Performed a cleaning and tune-up on the furnace and air conditioner.
Performed service on the geothermal system.
service gas furnace
Tempstar furnace cleaning