Performed the start up on a new furnace. No gas leaks detected. Gas and exhaust levels are normal. No CO detected in the air. Drain is working. Venting and exhaust components are properly installed. Heat rise was 47 degrees. High limit passed safety test. Unit is operating normally at this time.