Came out to investigate a no heat. Furnace was going off on a high limit code. I removed the limit switch, tapped it a few times to loosen the bearings and homed it out. Everything checkout out fine with the limit. I reset the rollout switch and everything kicked in. I cycled to unit a few times with no other failures. Unit is heating properly.
Checked pressures 10 degrees of sub cooling with a 18 degree temp split. Everything is currently operating normal at this time job complete
Was here for a furnace cleaning. Performed preferred customer furnace cleaning. Completed furnace cleaning form. Furnace is running normally at this time. Noticed that the air conditioner hasnâ€™t been checked since it was installed. Recommend getting an air conditioning clean and check in the spring. Office to bill the customer for the furnace cleaning.
Install new electrical service.