Polite and efficient. Happy with the service
Technicians did a great job fixing noise issues with the furnace
Performed the level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger looks good. Combustion readings were normal. No CO detected in the air. Drain is clear. High limit passed the safety. Heat rise was 44Â°. Unit is heating properly.
Performed the level 1 furnace safety check. Inducer motor is starting to wear. Heat exchanger has rust and metal chipping. There was also a lot of backdraft from the heat exchanger with the smoke test. Combustion readings were also a little higher than they should be. No CO detected in the air at this time. Average life of system is 12-15 years. Furnace is currently 20+ years old. Due to age, condition, cost to repair, and for safety measures, a second opinion is recommended with Dan Fox to consider options.
Installed Daikin Air Conditioner â€“ M#DX13SA0361AE S#1802012302 Installed Coil - M#CAUF3642C6 S#1807397375 Completed Air Conditioner replacement. Installed new coil and set condenser outside. Thank you for choosing Black-Haak. Please take a moment to fill out our online survey.
Installed insulated duct for return drop. We need 13â€ piece 23â€x9â€ was 9â€™ basement.
Checked out B-vent penetration and is correctly done. Also gave customer a run through of thermostat. Showed them where and gave them the user guide for future reference.
I completed a level 2 preferred customer cleaning on the Geo unit. I tested the electrical and found correct voltage from the contactor and capacitor. The contacts still look, no pitting. The compressor amps are at in good range at 11.2,15.3, and 10.1. On the heating side the heat of extraction is at 34,920 BTU. On the cooling side the heat of rejection is at 48,015 BTU. I changed the AprilAire 213 filter that was dirty. Adjusted the humidity settings at the thermostat because they have had some moisture on the windows. Recommend changing the humidifier out for a model 700 to eliminate the humidifiers bypass, as well as a whole home dehumidifier. Darren removed the drain trap and added a secondary drain off of the coil because it got plugged up a few times. The geo system is operating properly at this time. I wrote up an estimate for a dehumidifier and model 700 humidifier to combat the moisture issue on the windows.
Was here for a 1st year furnace cleaning. Performed 1st year preferred customer cleaning. Did not find any issues with the furnace. Furnace is running normally at this time.
gas boiler service
furnace replacement quote