Replaced the capacitor. Unit is cooling properly at this time.
I played with the T6 WiFi thermostats to get them connected to their network. After a little bit of problems I switched the WiFi network I was using and was able to get everything connected to their Honeywell account. The thermostats are on their network and operating properly with the app.
Was here for a package and a furnace cleaning. Performed preferred customer furnace cleanings on both units. Completed furnace cleaning form. The furnaces are running normally at this time. Performed preferred customer air conditioning cleaning. Completed air conditioning cleaning form. Checked the indoor coil for leaks. Didnâ€™t find a leak in the indoor coil. Checked the refrigerant levels. The refrigerant levels look good. Checked the electrical. Air conditioner is running normally at this time.
Completed AC replacement. Reclaimed old refrigerant and removed outdoor condenser and indoor coil. Installed new coil in furnace plenum and re-leveled existing pad and set new condenser on it. Flushed lineset and reconnected. Pumped up lineset with 325psi nitrogen to check for leaks then evacuated to 651 microns. Released charge and did a complete start up procedure. Thank you for choosing Black-Haak heating. Please take a moment to fill out our online survey.