Friendly, on time and very knowledgeable. They did an awesome job!
Gary Petrie was our service tech which in my opinion did an excellent job, communicated well, well mannered and conscience of our surroundings. I wouldn't mind having him come back every year to service our equipment!
All my experiences with Black Hawk have been very good. Service is timely, well done, generally well explained and service people always courteous.
Kody is always great
Punctual. Friendly, knowledgeable. Happy to have me look over his shoulder (to learn). Highly recommended.
Dan did a excellent job. He was very professional and a really nice guy. And very helpful.
I have used your electrical services twice. Both times your electricians have been great. All work has been well done and timely efficient.
Completed LP gas furnace replacement and new Aprilaire 600 installation. Disconnected and removed the old furnace. Set the new furnace on blocks and reconnected the gas, electric, pvc venting and ductwork. Installed a new T6 Wifi thermostat and connected it to the furnace. Installed an Aprilaire 600 humidifier on the return drop and connected all the wiring to the furnace. Run tested the furnace and humidifier but our office will contact you to schedule a technician start up for the new furnace. Thank you for choosing Black-Haak Heating and Electric. Please take a moment to fill out our online survey.
Completed installation of (2) 8â€ round pipes ducting the heat from both wood fireplaces to a common 10â€ pipe, and then into the return air drop at the furnace. Ran both 8â€ pipes above a finished ceiling approximately 30â€™ to an upper and lower fireplace, then attached each to a fireplace. Tied both runs into (2) separate inline fans that the homeowner provided, then attached them into a single 10â€ pipe which we attached to the furnace drop. Thank you for choosing Black-Haak Heating and Electric. Please take a moment to fill out our online survey.
Replace igniter for the second time. Furnace is operating at this time.
Furnace clean and tune. Cycled system. System has a large light off. Checked heat exchanger. Found that both chambers are rusted with deep etching. Checked and removed burners. Burners are very corroded and damaged. Unable to clean well due to the large amount of corrosion and rust. This is causing the flame to flower out across the heat exchanger. This is causing excess rusting and drop of efficiency. Igniter/flame rod is corroded. Igniter has etching and cracks starting to form. Found ventor motor bearings are very worn and this will cause the motor to seize. Found evidence of condensate leaking from behind and under ventor motor. Transition assembly may also be compromised. Found rusting in the blower compartment as well. Preformed combustion test. Found XS air to be higher than normal. Levels are around 175. No CO found in airstream. Average life expectancy for this unit is 14 years. This system is 22 years old and in poor condition. Due to age, condition, and cost of repair, secon
Removed and cleaned and reinstalled flame sensor Removed and cleaned and reinstalled gas burners Checked gas outlet pressure Checked igniter Checked filter and replaced Checked humidifier water panel and replaced Inspected and tested inducer motor and blower motor Checked your condensate drain trap Furnace working well at this time Tune ups maintain warranty
Installed inducer assembly Complete
Came out to check a loud noise. Customer said there were screws loose by the blower motor. I tightened the screws and cycled the furnace three times. I didnâ€™t hear any noise that was out of the ordinary. There didnâ€™t appear to be any damage to the motor or furnace. I adjusted the fan speeds to quiet down the motor a little. The screws on the aprilaire filter box were left from install. We usually leave some in case theyâ€™re needed later on. Everything is tightened down and unit is heating properly.
Delivered the filter. No answer. I left the filter at the door.
Performed the level 2 furnace cleaning. Burners and flame sensor had a lot of oxidation to clean off. Igniter ohmed a little high. Heat exchanger has a lot of rust, however, no cracks located at this time. Combustion readings were normal. No CO detected in the air. Drain is clear. High limit passed the safety check. Heat rise was 53Â°. Unit is heating properly at this time. Due to age and condition, I recommended keeping an open mind for options in the future. Life expectancy cannot be guaranteed.
Removed and cleaned and reinstalled flame sensor Removed and cleaned and reinstalled gas burners Checked gas outlet pressure Checked igniter Checked filter looks like you order your own Inspected and tested inducer motor and blower motor Checked your condensate drain trap found multiple bugs in trap Furnace working well at this time Tune ups maintain warranty
Performed a preferred customer furnace cleaning on the attic furnace. Cleaned the burners and the flame sensor. Checked the furnace heat exchanger. Wiped down the inside of the furnace. Checked the electrical. Cycled the furnace and performed a furnace combustion test. No issues with the furnace at this time. Basement furnace. Cycled system. Checked heat exchanger, minimal rust and corrosion. Checked and cleaned burners and flame sensor. Checked and adjusted gas pressures to maximize efficiency. Preformed combustion test. All readings were normal. No CO in airstream. Replaced filter. System operating normal at this time. Guest house furnace. Cycled system. Checked heat exchanger, ok. Checked and cleaned burners and flame sensor. Checked and adjusted gas pressures to maximize efficiency. Checked and cleared drain line. Preformed combustion test and found all levels normal. No CO in airstream. Recommend replacing filter on this unit. Job complete. Customer is interested in using MR POW
Repair leak. Chiseled more of the concrete out to repair pipe. Cut out punctured section of pipe and repaired with coupling. Pressure tested system. No leaks were found. Ran and tested boiler. All systems operating properly at this time. Thanks, Brennan and Brad
Replaced the T4 thermostat. Cycled the furnace. Unit is heating properly.
Removed and cleaned and reinstalled flame sensor Removed and cleaned and reinstalled gas burners Checked gas outlet pressure Checked igniter Checked filter Inspected and tested inducer motor and blower motor Furnace working well at this time. Please renew tuneups to maintain your warranty
Quoted pricing Will call to schedule