Performed the level 2 package cleaning. Furnace: Burners and flame sensor are clean. Heat exchanger looks good. Combustion readings were normal. Drain is clear. No CO detected in the air. Igniter ohmed okay. High limit passed the safety check. Heat rise was 42Â°. AC: No leaks detected. Electrical components from the compressor tested good. Capacitor is starting to test low. Condenser coil is clean. Refrigerant pressures were normal. Subcool was 10Â° with a 20Â° temp split. All equipment is operating properly.