Dan is not only good at what he does but he is even better at customer relations. I was very pleased with everything he did for our home
Black Haak has an outstanding workforce, all working in perfect coordination to get the job done quickly, efficiently, and correctly! They did an EXCELLANT job! Friendly, considerate, and courteous too...answering all questions, and very informative!
My service technician was very informative and friendly. They stand behind their products and respond in very reasonable amount of time.
Removed and cleaned and reinstalled flame sensor Removed and cleaned and reinstalled gas burners Checked gas outlet pressure Checked igniter Checked filter Inspected and tested inducer motor and blower motor Checked your condensate drain trap Furnace working well at this time Tune ups maintain warranty
Completed start up Checked gas valve and adjusted Checked for gas leaks No co in airstream 6ppm in flue System working well at this time
It is currently in its 14th heat season Inducer assembly replaced after 8 years 2014 Drain trap replaced after 9 years 2015 I can not remove the flame sensor to clean it as itâ€™s rusted on to the burner box Wire brushed gas burners Checked igniter Checked heat exchanger- some corrosion showing Adjusted hi and lo gas pressure to Oem specs System operating within parameters at this time This system has no warranty, homeowner to pay full costs
Furnace clean and tune. Cycled system. System fired. Checked heat exchanger with camera, found large crack in far left heat exchanger. This is an immediate fail of inspection. System has been disabled until options are given to customer. Black-Haak is not responsible for any injury or other if system is enabled by customer and ran. CO levels may be dispersed into the home causing harm. Black-Haak heating does NOT recommend running heat until system is fixed. Cleaned fireplace. Cycled system. Cleaned glass, walls, logs, igniting system and outside. System operating normal at this time. Job complete. Charges pending results of second opinion.
Preform furnace cleaning. Removed and cleaned burners, and flame sensor. Ohmed igniter. Inspected electrical, gas piping and venting. Removed and cleaned drain trap, and cleared drain lines. Preformed combustion analysis. All systems operating properly at this time. Have a wonderful fall, Brennan
Furnace not heating and just blowing cold air. When I arrived she had the unit turned off so I cycled the unit. Ventor motor did not turn on so I tested voltage, 120 volts to the motor and furnace would go out on pressure switch open. Blower motor is also slow to start up. Talked to her about repair vs replacement options. Dan will call her to talk about the options for replacement. Thanks Brad If you could take a few minutes and fill out a quick survey on how I did today, I would greatly appreciate it.
Performed a furnace start up. Checked over the furnace installation. Cycled the furnace. Set the gas pressure and checked the fan speed. The furnace is running normally at this time.
Performed the level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger looks good. Combustion readings were normal. No CO detected in the air. Drain is clear. High limit passed the safety check. Heat rise was 40Â°. Water panel and furnace filter were replaced. Unit is heating properly.
Performed the level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger looks good. Combustion readings were normal. No CO detected in the air. Drain is clear. High limit passed the safety check. Heat rise was 42Â°. Unit is heating properly. I also helped the customer set up there WiFi stat with the Honeywell app.
9/4 Started generator install 9/5 Finished generator install
Performed the level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger looks good. Combustion readings were normal. No CO detected in the air. Drain is clear. High limit passed the safety check. Heat rise was 45Â°. Unit is heating properly.
Furnace clean and tune. Cycled system. Checked heat exchanger. Found all chambers are rusted and worn. No visible cracks found at this time. Removed, checked, and cleaned burners and flame sensor. Both were rusted, but ok. Checked electrical connections and clamps. Checked and adjusted gas pressures to maximize efficiency. Checked for levels of XS air and CO in exhaust. Normal l vela found. No CO found in airstream. Ac. Replaced filter. Cycled system. Checked and cleaned electrical compartment. capacitor tested low. Used coil cleaner on condenser coil. Hooked up gauges and tested pressures and temps. Found subcooling was 10, indoor coil temp was 40, indoor temp split was 15. System is worn, but operating normal at this time. Job complete. Office to bill for this job.
Ac clean and tune. Cycled system. Checked filter. Checked electrical compartment. Contactor and capacitor ok. Used coil cleaner on condenser coil. Hooked up gauges and checked pressures and temps. Subcooling was 10. Indoor coil was 39. Indoor temp split was 18. System is operating normal at this time. Job complete.
Ac clean and tune. Checked drain line. Checked filter. Cycled system. Checked electrical compartment and cleaned. Capacitor and contactor tested ok. Used coil cleaner on condenser coil. Hooked up gauges and checked pressures and temps. Found that the subcooling was 10. Indoor temp split was low. Adjusted fan speed down to blue to increase temp split up. Split was up to 17. System is slightly over charged, but operating normal at this time. Job complete.
Performed the level 2 AC cleaning. No leaks detected. Electrical components tested good. Condenser coil is clean. Refrigerant pressures were normal. Subcool was 8Â° with a 17Â° temp split. Unit is cooling properly.