Very professional, did a great job, answered questions.... very happy with the service.
Couldn't be happier with our decision to use Black Haak for installation of our new air condition system! Great customer service, fast installation (had to quit early one day due to rain, but still finished ahead of time) and the products work just as the salesman said they would.
Did excellent work. Very thorough.
Performed the level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger looks good. Combustion readings were normal. No CO detected in the air. Drain is clear. High limit passed the safety check. Heat rise was 36Â°. Unit is heating properly.
Ac clean and tune. Checked indoor coil for leaks worn refrigerant sniffer. No major indications found at this time. Cycled system. Checked electrical compartment. Ok. Used coil cleaner on condenser coil. Hooked up gauges and checked pressures and temps. System is worn , but operating normal at this time. Furnace clean and tune. Cycled system. Checked and cleaned burners and flame sensor. Both ok. Checked igniter, ok. Heat exchanger is normal at this time. Checked for levels of CO and XS air in exhaust. Normal levels found. No CO found in airstream. System operating normal at this time. Job complete. Checked fireplace. Found that the gas valve was off. Tried to find gas shut off for fireplace, unable to locate. Fireplace is located in a room with no basement access under it. Checked ignition system. It is dirty. Cleaned sparker and flame sensor as well. Tried to light pilot with ignition sparker, unable to do so. Removed glass and lit manually. Was able to light pilot. Gas valve appea
Performed the level 2 AC cleaning. No leaks detected. Electrical components tested good. Condenser coil is clean. Refrigerant pressures were normal. Subcool was 8Â° with a 17Â° temp split. Unit is cooling properly.
Performed leak search; found leak in high side braze joint at the condenser, soldered joint and releases charge, added 1 pound of refrigerant bring our subcooling up to 8 degrees as well as a 17 degree temp split. This system is currently operating normal at this time. I am including a quote for an electronic air cleaner this will reduce the allergens and particles in he home dramatically compared to the allergen filter in place. Job complete
Performed the package cleaning. Furnace: Burners and flame sensor are clean. Heat exchanger looks okay. Combustion readings were normal. Drain lines are clear. No CO detected in the air. High limit passed the safety check. Temp rise was 69Â°. Only thing I found is the rust from what appears to be water damage awhile back. No standing water or leaks at this time. AC: No leaks detected. Electrical components tested good. Capacitor tested in the required zone. Condenser was cleaned with water and nu brite. Refrigerant charge was normal. Superheat was 11Â° with a 20Â° temp split. All HVAC equipment is operating properly.
Performed AC safety check; sniffed the evaporator coil for potential leaks, cycled the AC on to verify operation, I did inspect the electrical compartment the capacitor is 10 years old and is showing definite signs of wear I would recommend getting this replaced with the AC clean and tune, the outdoor coil is getting plugged with cotton and other debris i highly recommend getting this system cleaned on a warmer day so we can spray down the outdoor coil with a chemical solution as well as to check pressures on the system to prevent any future issues. This system is currently operating normal at this time. Job complete
Furnace start up. Cycled system. Checked electrical system, ok. Checked incoming LP gas pressure. Found incoming was 10.65 IWC. No regulator found on gas line. Water heater is electric. Adjusted outgoing gas pressures to maximize efficiency. Checked for gas leaks, none found. Checked for CO and XS air in exhaust, normal levels found. No CO found in airstream. Checked temp rise and fan speed, ok. System operating normal at this time. Job complete.
Performed a first year furnace cleaning. Cleaned the the burners and the flame sensor. Checked the furnace heat exchanger. Wiped down the inside of the furnace. Cleaned the drain trap and drain line. Cycled the furnace. Checked the motors for proper operation. Performed furnace combustion test. The furnace is running normally at this time.
Completed Gas Furnace replacement. Disconnected and removed old furnace and then set new one on blocks in its place. Reconnected the gas, electric, PVC vent pipes, and duct-work to new furnace. Put a new WiFi Thermostat by the drop. Run tested the furnace, but will still need a technician start up. The Office will follow up to schedule a technician to return to do the Furnace efficiency startup, which is required for warranty purposes. Thank you for choosing Black-Haak Heating. Please take a moment to fill out our online survey.
was Here on no heat found the main board to be bad also under additional work replaced igniter and psi switch. Also we are crediting the charges from this morning to his new bill
Performed furnace start up; customer stated that they would like their humidifier wired into Nest Tstat I ran a new 8 wire for this and spoke with Nest we will have to return to finish the wiring, I then inspected the exhaust and intake PVC ensuring all connections were secured, I then sniffed the gas line for possible leaks, next I cycled the system on and checked gas pressures and did make adjustments on both stages, lastly performed a combustion test verifying no CO in the airstream. This system is currently operating normal at this time. Job complete
Furnace wasnâ€™t heating and I couldnâ€™t read the codes. Cycled furnace. O igniter but the gas came on. 120v to the igniter and igniter is open. Talked to customer about the issue and repair vs replacement. They was tied to get heat on and are planning to replace the furnace early next year. Gave the customer on option of prefoming a cleaning. Replaced th igniter and tested the heat exchanger and preformed a combustion test to insure safety. Everything operating properly. Thanks Brad
Installed Daikin Furnace - M#DM96VE060 S#1805735877 I completed the gas furnace replacement. I disconnected and removed the old furnace. I set the new furnace on blocks and reconnected the electric, gas, pvc venting and duct-work. I ran a new condensate drain line to the floor drain. I installed the customer provided Nest thermostat per their request. I run tested the furnace, but will still need a technician to complete the start up. Thank you for choosing Black-Haak heating. Please take a moment to fill out our online survey.
Completed gas furnace replacement. Disconnected and removed old furnace. Set new furnace on blocks and reconnected the electric, gas, pvc venting and ductwork. Ran a new condensate drain line to the floor drain. Installed customers Nest thermostat per their request. Run tested furnace but will still need a technician start up. Thank you for choosing Black-Haak heating. Please take a moment to fill out our online survey.
All registers are installed.