Great job! Appreciate ability to get the job done quickly.
Excellent job! Appreciate the quick service.
Very good experience, high knowledge of products and services. Overall great experience. And would recommend to anyone
Did a great job explaining my options, ordering and installing my air conditioner, in a very timely manner. Communication from start to finish was accurate and informative, very helpful in understanding my options. Air conditioner was installed and is working properly. A few years back you installed my furnace, very happy with both installations. Thank you!
Dan was our technician, and I can't say enough good things about him! He is so personable, and did a great job. He explained things well, and worked hard to make sure I knew what all my options were. He also went out of his way to have me talk to another member of the Black Haak company to see if replacing my furnace would be a better option. Dan understood when we couldn't afford that right now, and didn't push us to go beyond our budget. He was a really great guy!
Performed preferred customer air conditioning cleaning. Checked the indoor coil for leaks. Did not find any leaks in the indoor coil. Cleaned the condenser coil. Checked the electrical. Cycled the air conditioner and checked the refrigerant levels. The refrigerant levels are normal. No issues with the air conditioner at this time.
Changed breaker for ac
Found water in blower compartment of furnace. Customer indicated that water started leaking this past weekend. Cycled system and checked pressures and temps, ok. Removed filter. Filter was very dirty. Recommend ac clean and tune. Possible tipping coil to drain a little more. This situation not from furnace instal or operation. Office to schedule. System cooling at this time. Job complete.imstall crew noticed coil pitched incorrectly, recommended repairs at that time. Customer did not call back to schedule.
Quoted and emailed estimates, .
Performed preferred customer air conditioning cleaning. Checked over the air conditioner. Did not find any issues with the air conditioner at this time.
Returned to replace main board and to do AC start up. Added 1.5 pounds of refrigerant for a sub cool of 10 degrees with a 20 degree temp split. This system is currently operating normal at this time. Job complete
Performed the level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger looks good. Gas and exhaust levels are normal. No CO detected in the air. Temp rise was 40Â°. High limit passed the safety test. Unit is heating properly.
Performed the level 2 furnace and AC cleaning. Furnace: Burners and flame sensor are clean. Heat exchanger looks good. Combustion readings were normal. No CO detected in the air. High limit passed the safety test. Temp rise was 40Â°. Unit is heating properly. AC: Leaks detected outside. Electrical components are getting bad. I had to remove a mouse nest from the electrical compartment. Refrigerant tested very low. Average life of system is 12-14 years. Unit is currently 20+. Due to age, condition, and cost to repair, second opinion is recommended. Failure is expected in the future.
Was here for a package cleaning and to clean the mini split air conditioner. Performed furnace cleaning. Found moderate to heavy rusting in the heat exchanger. Electrical components are original. Performed combustion test. The furnace is 16 years old. Recommend continuing to get cleanings to monitor the heat exchanger. The furnace is running normally at this time. Performed air conditioning cleaning on the mini split unit. Found that a mouse got into the electrical and was causing the air conditioner to not start up. Cleared out the mice. No damage to the electrical. Cleaned and cycled the air conditioner. The air conditioner is running normally at this time. Performed air conditioning cleaning on the Armstrong unit. Checked the indoor coil for leaks. Found indications of a leak in the indoor coil. Found that the air conditioner is low on r-22 refrigerant. This unit is 16 years old. Recommend my supervisor give the customer a call.
Cycled ac system. Hooked up gauges and checked pressures and temps. Found subcooling at 10, indoor coil temp at 40 degrees, indoor split was 18. This was achieved after 15 mins of run time. Pressures and temps are ok. System set up correctly. Job complete.
Performed package clean and tune. Started with the furnace inspected the exhaust and intake PVC ensuring all connections were secured, removed and cleaned the burners along with the flame sensor, cycled system on and checked gas pressures, as well as performed a combustion test verifying no CO in the airstream. Made my way to the outdoor condenser. I inspected the electrical compartment and tested components, sprayed down the condenser with coil cleaner, cycled AC on and checked pressures and temps super heat 19 degrees with a 20 degree temp split. These systems are currently operating normal at this time. Job complete
Ac start up. Checked disconnect. Checked high voltage wiring to condenser. Checked low voltage two wire to unit. Hooked up gauges. Found system charge was dropped due to ambient temps and pressures. Found valves open. Checked two wire in furnace, ok. Checked filter, ok. Cycled system. Checked pressures and temps. Subcooling was 11 with outdoor temp at 58. Split was 17. System has correct charge, but would like to verify and fine tune when temps are higher and there is a heat load in home. System is operating at this time. Job complete.
Performed the AC check. I found indications of leaks at the indoor coil and outside by the unit. Contactor was worn and tested out of its zone. Customer said the indoor coil froze up last year. The leaking R22 is most likely the cause. The unit is currently 17 years old. Average life of system is 12-14 years. Due to age, condition, and cost to repair, second opinion is recommended. We will call to schedule.
Ran wires and surface mounted a new duplex outlet on wall for WiFi extender.