We had Jeramiah and I love that guy! Very helpful and always asks if I have any questions which I did and he answered. Love the fact that all the technicians that come to my home always put on shoe covers! I appreciate that!
What a great team you have at B-H. I really appreciate every step you took in solving my problem with my Generac generator during the storm.
Remove wiring from hot tub.
Performed AC start up; connected low voltage wires to terminal strip and to contactor on the condenser, released nitrogen and pulled vacuum to 360 microns, released compressor charge and removed a half pound of R410, superheat is at 16 degrees with 10 degrees of sub cooling with a 17 degree temp split. This system is currently operating normal at this time job complete. Inspected Tstat to see if we could connect to WiFi its a Honeywell prestige which will need a red link gateway
Performed furnace start up; started by setting up the humidifier at the prestige thermostat, I then went and inspected the exhaust and intake pvc ensuring all connections were secured, I then did a leak search on the gas line, I cycled the system on and checked gas pressures and did make adjustments on both stages, lastly performed a combustion test verifying no CO in the airstream. This system is currently operating normal and heating at 58 degrees at this time job complete.
Service call for the furnace not heating. Replaced the faulty thermostat.
gas boiler cleaning
Installed a Magneto kit for the Generac generator.
Generac generator service
Finish air conditioner install
Install central air conditioner