The guys did awesome job and very polite
Dan answered all my questions and was very honest about my situation.
Found that the broken part was under manufacturer's warranty even though the furnace was installed by another company 4 years ago. Saved me $200. Great service! Thank you!
Thank you to Black-haak and Corey for exceptional service.
Replaced generator and transfer switch. 10/30. To do start up once generator has gas to it. Gas piping and generator walk through with moch transfer 10/31. Job completed
Black Haak will need to upsize the main gas pipe from 3/4â€ to 1â€. This will bring your gas line up to code and ensure all appliances will run at their peek performance. Upsized incoming main gas line to appropriate size. Reconnected all gas lines. Piped new generator. Checked for leaks and relit all appliances.
Performed first year furnace cleaning; started by inspecting the exhaust and intake pvc ensuring all connections were glued, next I cleared out some blockage from drain line, I replaced 16x25x1 filter, next I removed and cleaned burners along with the flame sensor, then i cycled the system on to check gas pressures found 1st stage at 2.9 Inwc and found second stage cutting off as soon as it would engage. I adjusted 1st back down to 1.9inwc, and found a loose wire going to a pressure switch. Lastly performed a combustion test verifying no CO in the air stream. This sytem is currently operating normal at this time job complete
Pkg clean and tune. Furnace. Cycled system. Checked heat exchanger. Checked and cleaned burners and flame sensor. Checked igniter. Checked for co in airstream, none. Normal levels of CO in exhaust as well as normal levels of XS air. Furnace operating normal at this time. AC. Cycled system. Checked electrical compartment. Contactor showing signs of ware. Compressor tested normal. Hooked up gauges and checked pressures and temps. Found super heat and sub cooling at 0. Head pressures were up to 350 psi. Coil temp was 50. Cleaned condenser with coil cleaner and re checked pressures and temps. Sub cooling was 18. Super heat was 0 with a coil temp of 30. System is low on refrigerant. Split was 13. Average life of this system is 14 years. This system is 24+ years old and in poor condition. Due to age, condition, and cost to repair, second opinion is recommended. System failure is expected. Job completed.
Was here for a furnace cleaning. Customers neighbor let me in. Performed preferred customer furnace cleaning. Completed furnace cleaning form. Did not find any issues. Furnace is running normally at this time. Changed the furnace filter and the humidifier pad filter. The air conditioner hasnâ€™t been checked in over a year. Recommend getting an air conditioning cleaning. Office to bill the customer.
Performed level 2 AC cleaning. No leaks detected at indoor coil. Electrical components tested good. Condenser coil is clean. Refrigerant charge was good. Unit is operating normal at this time.
Ac installation complete.
Dispatched to pkg clean and tune. Cycled ac. Customer stated that the indoor coil and suction line was freezing up and there was water in the basement floor. Used refrigerant sniffer on indoor coil and found several leaks. Hooked up gauges to check pressures and temps. System was several pounds low of R-22 refrigerant. Second opinion set up with Dan F for today. No charge for safety inspection, pending results of second opinion. Cleaning not done due to issues found. Furnace Cycled system. Checked heat exchanger, rusted. Checked igniter and flame rod. System was cleaned. Checked for co in airstream, found none. Normal co found in exhaust, system operating normal at this time. Job complete.
Venting not up to code going out the roof needs more pipe added to it, 6â€ air jet b-vent. No gas leaks detected with my meter checked before and after the cleaning son all gas joint and gas valve. Gas leak may have been from the gas burner install wrong from another service call. Performed cleaning on boiler. Preformed combistion Anaylasis CO: 27 O2: 8.1 CO2: 7.3 excess air: 63.2. Boiler operating safely at this time.
Performed a clean and tune up on the furnace. Found the flame sensor was dirty and burnt up. Weâ€™ll call back with a price to replace the flame sensor. This is what was causing the furnace to not heat. The furnace is operating at this time. Call to schedule rick to come out and give geo thermal estimate. Call to give price for flame sensor replacement Weâ€™ll come back in the spring to clean ac.
Installed electrical switches.
Found a total of three leaks in the system. 2 in the worship area radiators. Boiler leaks where on unions and tighten them up to seal them. Cycled the upstairs no other leaks found. Checked downstairs. Found a steam trap cap leaking, tighten it up system opperating properly at this time. We where getting shocked all around the church didnâ€™t matter what register we touched we got shocked. Talked to Jamie we will have one of the electricians take a look at it.
Wire basement family room and bar switch (1) set of 3ways for family room and (1) single pole for bar.
Performed a cleaning and tune-up on the gas fireplace.