Great Price and Service from Black Haak Heating. I would recommend them for all your heating needs😎
Dan was friendly and very professional and knowledgeable
Quick response time, friendly service, very pleased with product options and would recommend black-haak to others.
Removed original 4â€x10â€ box that was too deep and replaced it with a more shallow one that doesnâ€™t protrude past framed wall on unfinished side. Installed a #213 Aprilaire upgrade kit with a new filter for the existing Spaceguard 2200. Thank you for choosing Black-Haak Heating and Electrical. Please take a moment to fill out our online survey.
Performed the level 2 furnace cleaning. Burners and flame sensor are clean. Heat exchanger has rust and chipping. Unit did fail the smoke test, however, there were no cracks located and the combustion readings were normal. No CO detected in the air. Drain is clear. High limit passed the safety check. Heat rise was 47Â°. Unit is heating properly. When we return for the duct work, we will need to bring a 213 upgrade kit and filter.
Performed preferred customer furnace start up. Checked over the furnace installation. Cycled the furnace. Set the gas pressure and the fan speed. The furnace is running normally at this time.
Performed the level 2 AC cleaning. No leaks detected. Electrical components tested good. Condenser coil is clean. Refrigerant charge was normal. Subcool was 8Â° with a 17Â° temp split. Unit is cooling properly.
Wired pool pump and heater. Installed pool bonding ring.
**DO NOT GO HERE - PLEASE ADD M# & S#** Installed Daikin Air Conditioner â€“ M#DX13SA0241AF S#1903349968 Installed Coil - M# S# Completed Air Conditioner replacement. Installed new coil and set condenser outside. Thank you for choosing Black-Haak. Please take a moment to fill out our online survey.
Performed the level 2 furnace cleaning. The unit is showing signs of wear. Heat exchanger is very rusty and chipped. I performed the heat exchanger smoke test and had a lot of back draft. No cracks located and no CO detected in the air at this time. Ventor motor, burners, and flame sensor are all starting to wear out as well. Average life of system is 12-14 years. The unit is currently 14 years of age. Due to age, condition, and cost to repair, second opinion is recommended. Furnace is currently okay to run, however, we cannot garauntee how long it will be safe and we canâ€™t give any sort of life expectancy for the future.
Performed AC and Furnace start ups; connected low voltage wires to condenser, released nitrogen from system and dropped charge, had to add 12 ounces of 410 refrigerant to the system to bring sub cool up to 9 degrees. System is currently operating normal and cooling at 20 degrees. I then cycled the furnace on checked/adjusted gas pressure, performed a combustion test verifying no CO in the airstream, inspected exhaust and intake PVC ensuring all connections were secured. Due to the amount of dust inside the furnace i am including a quote for an electronic air cleaner to help bring the down the levels of particles in the home for better air quality as well to relive strain on the system. Everything is operating normal at this time job complete
Performed preferred customer air conditioner cleaning. Did not find any issues with the air conditioner at this time.
Performed level 2 furnace cleaning. I found the drain trap was leaking. Part was replaced under warranty. No more leaks or standing water at this point. Burners and flame sensor are clean. Heat exchanger looks good. Gas and exhaust levels are normal. No CO detected in the air. Heat rise was 42 degrees. Unit is operating normally at this time.
Furnace clean and tune. Cycled system, checked heat exchanger, found some rust in heat exchanger but no cracks are visible at this time. Checked igniter, showing signs of being worn, but tested ok at this time. Checked and cleaned flame sensor and burners, both are ok at this time. Checked and adjusted gas pressures to maximize efficiency. Checked for CO in airstream, none found. Normal levels of CO and XS air found in exhaust. System has some signs of being worn, but is operating normal at this time. System longevity will improve with yearly maintenance. Job complete.
1/3/19. Removed old furnace. Installed new daikin furnace. Installed metal to connect new furnace to duct. Reconnected electrical and thermostat wiring to furnace. Ran gas line to new furnace. Ran all new drain hose from furnace and coil to floor drain. Hooked pvc venting to new furnace. Started furnace and everything is running as it should. Thank you for choosing Black-Haak heating for your heating needs.
Furnace clean and tune. Cycled system. Checked heat exchanger. Found both shots are rusted. No visible cracks at this time, but deep rust and etching found. Checked and cleaned flame sensor and burners. Found igniter worn. Checked and adjusted gas pressures to maximize efficiency. Found normal levels of Co And XS air in exhaust. No CO found in airstream. Found ventor motor bearings are worn and grinding during all portions of operation. Large rust spot from water leak found in burner compartment. System is operating safely at this time, but failure is expected. Second opinion is strongly recommended due to age, condition, and cost to repair. Failure is expected. Job complete.
Performed furnace clean and tune. The furnace is operating properly at this time. This was already paid for.
Furnace clean and tune. Cycled system. Checked heat exchanger, found it very rusted with cracks starting to form. Found igniter/flame rod is worn. Transition assembly is leaking. Some standing water in burner compartment. Rusting from leak in blower compartment. Ventor motor bearings showing signs of being worn. Checked for CO and XS air in exhaust. Normal XS air and CO found. Checked for CO in airstream, none found. Average life of this unit is 14 years, this unit is over 19 years old and worn. Future failure is expected. Second opinion recommended. System is worn, but operating normal at this time. Job complete.