Jeremy was excellent in helping my wife and I with our inspection. Definitely went above all expectations to make sure we understood the process and completed job and more in A+ fashion
Response from Bradbury Brothers Cooling, Heating & Plumbing:
Thank you so much, Dan! Our goal is 100% satisfaction with our people, products, and services. We are so excited to hear that we received an A+ from you! Thank you for giving us the opportunity to serve you.
Not completely satisfied with the small service fee that was charged because this was a follow up request for a previous call that was not resolved. Still, I highly recommend Bradbury Brothers and their service over the years have been excellent !!
Heater making noises. Heating repair and maintenance tune up. Diagnose and perform annual heater maintenance service plan on York heating system. Replace capacitor and check furnace on 12 year old HVAC system. Heater maintenance complete which will help lower heating cost for this residential customer. R22 refrigerant will be phased out in January 2020. Recommend replacement with new Comfortmaker air conditioning system. Heating system is now ready for winter weather.
Heater not turning on. Heating repair and maintenance tune up. Diagnose and perform annual heater maintenance service plan on Daikin heating system. Add freon and check furnace on 10 year old HVAC system. Heater maintenance complete which will help lower heating cost for this residential customer. Filters are dirty. Filters should be changed monthly for best performance. Heating system is now ready for winter weather.
Hot water heater not making hot water. Diagnose and find water heater is over 8 years old and should be replaced. 8 year old Rheem water heater. Recommend replacement Rheem tank water heater, or Navien tankless water heater. Average water heater life span is 8-12 years old. Install new Navien tankless water heater with new pan and test for functionality. Recommend Gemline water softener to protect new water heater from hard water damage.
System: Downstairs Approx Age of System: 3 Combustible Gas Leak Detection Pipe and fittings leak-free: yes Valves and orifices leak-free: yes Carbon Monoxide Testing Walk-around CO: pass/ppm-0 Airside CO: pass/return ppm-0 supply ppm-0 Flue gas CO: pass/ppm-35 Ignition and Combustion Delayed ignition: no Flame disturbance: no Flame discoloration: no Motor Amperages and Capacitors Blower motor FLA: 5.6 Induced draft/combustion blower motor FLA: .6 Capacitor(s): pass Temperature Rise Rated: 25-55 Actual: 43 Static Pressures Blower speed/cfm: RP- .36 /FS- .22 /SP- .1 TESP: .58 Safety Controls Primary limit test: pass Filter sizes: 20x25x1 Changed filters: no. Itâ€™s clean. Scheduled next tune up date: Notes: ________________________________________ System: Upstairs Approx Age of System: 3 Combustible Gas Leak Detection Pipe and fittings leak-free: yes Valves and orifices leak-free: yes Carbon Monoxide Testing Walk-around CO: pass/ppm-0 Airside CO: pass/return ppm-0
Diagnostic System: Amana Refrigerant Type R410A Metering Device-TXV SP/HP 58/225 SLT/LLT 81/78 VSAT/LSAT 7.4/77 SH/SC 73/0 Outdoor Entering Air Temperature 75 Notes: Customer stated that her ac unit isnâ€™t cooling properly. On arrival checked tripped float switches and none found tripped, did find traces of water in the emergency drain pan. Then went to condenser and checked for normal operations and found condenser refrigerant charge was low. Spoke with customer about findings and did inform her that system has a possible leak, and until leak is repaired system is at high risk of refrigerant leaking out. Customer chose to add refrigerant at this time added 4lbs of 410-A to get unit back cooling and would like to have office check warranty and see what the next step would be. Added refrigerant and checked temperature split between return and supply, unit has 15 degree temperature split. Unit is cooling at this time. Recommendations:
Recommending navien tankless water heater and gemline water softener
Installed 12x12 return in master bedroom
Lennox ac tune up.
Diagnostic on Goodman system.
Diagnostic on Payne system.
Performing semiannual air conditioning maintenance tune-up on two Heil and Bryant AC systems for a residential Comfort Club member. Programming thermostat, checking air filters, testing safety controls/detectors, balancing airflow, assessing ductwork, taking vital readings, and evaluating HVAC system performance. Systems are cooling and ready for Summer weather.
Daikin ac tune up.
Bryant ac tune up
Fixing duct work!
Extending flue vent from install