Tested no hot water in back bathroom. Tested and found correct power to unit but we are not getting any element readings, typically a element issue. Verbal Maggie to replace element. Replaced element and tested.
Air conditioner not cooling. Air conditioning repair and maintenance tune up. Diagnose and perform annual AC maintenance service plan on Rheem cooling system. Clear drain lines and check evaporator coils on 5 year old HVAC system. AC maintenance complete which will help lower cooling cost for this residential customer. R22 refrigerant is no longer available in the United States. Recommend replacement with new Comfortmaker air conditioning system. Air conditioner is now ready for March weather.
Upon arrival found thermostat completely blank. Checked indoor unit found water backed up causing inline safety switch to cut unit off. Unit is out install from about 1yr ago. Unit has blowout valve missing, unit has safety pan switch, in-line switch but no blowout valve for access to clear/flush drain lines. Got in contact with on call manager for today and informed him issue, he stated if I could let water from the in-line switch out just for right now and he will get install back out here tomorrow to do corrections and install blowout valve, clear drain line. I have drained the water out from the in-line switch, unit kicked on right away and informed customers the issue that was happening, I informed them Iâ€™d rather for them not to run the ac due to water backing up again to the in-line switch and causing issue to happen again. Customer is now aware. I have left unit off right now indoor temperature is at 72. No other issues were visible, recommended plumbing special, customer sig
Check for bad smell. Also they stated when a toilet is flushed it makes the other toilet gurgle. Open ceiling tiles over bathroom and found sewer vents were not finished during rough in which will cause the bad smell on certain days. As for the gurgling recommend running camera to see if there is a blockage or see if correct fittings were used under slab.
Installing 3.5 Ton Comfortmaker Air Handler, Heat Kit, and Air Conditioner.
Cleanout trench drain on commercial building
Rewire AC unit for proper capacitor operation. Recommend AC tuneup.
Ac Tune Up
Run camera in sewer line, locate blockage and break up blockage.
Pull urinal and run sewer machine.
Unclog men's bathroom and adjust toilet to flush better.
Provide estimate to replace Rheem water heater.
Repair leak with schedule 80 male adapter and other fitting to get pipe out of bind from the fence post.