Earnest is very knowledgeable and I feel confident when he inspects our units
Response from Bradbury Brothers Cooling, Plumbing & Electrical:
Thank you, Stephen! We are excited to hear you enjoyed your visit from Ernest. We aim for 100% satisfaction with our people, so we are so glad to hear this. Thank you for taking the time to leave us this review!
System-downstairs Approx Age of System:11 Refrigerant Type- R410a Metering Device- TXV SP/HP:79.9/216.9 SLT/LLT:62.6/74.9 VSAT/LSAT- 20.9/74.1 Superheat/Subcool-41.5/-.6 Outdoor Entering Air Temp-69 Outdoor Fan FLA- .7 Compressor RLA/LRA-8.4/55 Contactor Voltage-242.3/25.9 Capacitor Rating-44.81/5.09 Indoor Return Dry Bulb Temp-70.1 Return Wet Bulb Temp-61.5 Supply Temp- 58 Temperature Difference-12.2 Required Difference-16-20 Blower FLA- 2.1 Filter Sizes â€“14x25x1(2) Changed Filters â€“ N Recently replaced Blew out drain line: N (No blow out valve ) Notes- System-upstairs Approx Age of System:11 Refrigerant Type- R410a Metering Device- TXV SP/HP:116/228.5 SLT/LLT:54.6/74.8 VSAT/LSAT- 38.7/77.8
System: Downstairs Approx Age of System: Combustible Gas Leak Detection Pipe and fittings leak-free: N/A Valves and orifices leak-free: N/A Carbon Monoxide Testing Walk-around CO: pass/ppm 0 Airside CO: pass/return ppm 0 supply ppm 0 Flue gas CO: N/A Ignition and Combustion Delayed ignition: N/A Flame disturbance: N/A Flame discoloration: N/A Motor Amperages and Capacitors Blower motor FLA: 2.4 Induced draft/combustion blower motor FLA: N/A Capacitor(s): fail/mfd 12.8/15 (6%/14.1) Temperature Rise Rated: 20-50 Actual: 31 Static Pressures Blower speed/cfm: RP .21 /SP .12 TESP: Safety Controls Primary limit test: pass Filter sizes: Changed filters: yes or no Scheduled next tune up date: Notes: 20.2 amps at heat strips. Run capacitor is operating below rated value. _______________________________________ System: Upstairs Approx Age of System: Combustible Gas Leak Detection Pipe and fittings leak-free: N/A Valves and orifices leak-free: N/A Carbon Monoxide Testing Walk-a
Performing semiannual air conditioning maintenance tune-ups on wo Tempstar AC systems in a residential home. Programming thermostat, checking air filters, testing safety controls/detectors, balancing airflow, assessing ductwork, taking vital readings, and evaluating HVAC system performance. Installing Turbo 200 condenser, compressor saver, Sanuvox Saber Pro UV treatment system, and UV bulb. System is cooling and ready for Summer weather.
Perform heat tuneup on comfort club member’s systems.
Performiing diagnostics on ICP air handler
Heating and ventilation inspection and evaluation.
Get furnace ready for the heating season.
Repair two leaks under kitchen sink and one leak under laundry sink.
Collect information for future repairs.